Relay: Differential current relay improves worker safety
Littelfuse RCD300M2 differential current relay improves worker safety and protects equipment from electrical ground faults. If fault current exceeds the relay trip setting, it activates and sends a signal to disconnect high potential from the equipment. Here's how it avoids an arc flash. Links are provided to other power protection products.
Littelfuse RCD300M2 differential current relay improves worker safety and protects equipment from electrical ground faults.
Des Plaines, IL – The Littelfuse RCD300M2 differential current relay improves worker safety and protects equipment from electrical ground faults. Unintended conductive paths from a high potential line to ground, allow electrical currents to pass through sensitive equipment components or through personnel who touch equipment housing with devastating results. About 90% of ground faults occur slowly due to dust buildup, moisture ingress, vibration, cable chaffing, or chemical and corrosive vapors, which lead to earth-leakage or residual-current ground faults that escalate to high-current levels. Annually, appoximately 150 fires and explosions in commercial and industrial buildings are caused by electrical grounding failures, with an average loss of more than $575,000 per event (per FM Global). The worst are dangerous arc-flash events.
To avoid nuisance tripping with conventional ground fault relays, maintenance workers tend to increase trip points above sensitive levels, which defeats the purpose of having a relay sensitive enough to protect workers from electric shock or arc-flash incidents. RCD300M2 uses technology that provides highly sensitive protection, avoiding nuisance trips and unnecessary equipment shutdown.
The relay is connected to a Littelfuse WKE Series current transformer (CT), and together they sense fault current. Advanced filtering techniques differentiate between fault current and typical noise or harmonic current. If fault current exceeds the relay trip setting, it activates and sends a signal to disconnect high potential from the equipment. Seven CT sizes are available for a range of wire gages and applications. RCD300M2 can operate in a fail-safe mode by continuously checking the CT connection. If the circuit is broken, it illuminates the CT Fault lamp and activates its disconnect relay, just as if a ground fault had occurred.
Features include automated monitoring and control in power distribution panels, switchboard installations, municipal utilities, elevators, new construction sites, and similar applications, plus an adjustable time delay (0-1.5s), fault indicator LEDs, and signal output to drive a remote meter or PLC. The output gives RCD300M2 protective and predictive capabilities; leakages can be seen as they develop, and ground faults can be detected before they are critical.
Specifications include adjustable trip setting: 10 mA to 3 A; relay supply voltage: 24 V ac/dc, or 120 V ac, 50-60 Hz; two form C alarm relay contacts: 1,100 V A switching capacity (closure); 5 A continuous current; 250 V rating; breaking capacity: 3 A @ 240 V ac (P.F. = 0.4), and 0.3 A @ 110 V dc (resistive load).
Also read about:
– Control Engineering News Desk
Register here and scroll down to select your choice of eNewsletters free.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.