Induction motors with autotransformers
Bruce Konzak writes:Dear Control Engineering: Does a single phase 240 Vac induction motor have the same performance characteristics when powered by an autotransformer with a line to neutral feeder, as it does when powered normally by a line-to-line connection 120 degrees out of phase?
Bruce Konzak writes:Dear Control Engineering: Does a single phase 240 Vac induction motor have the same performance characteristics when powered by an autotransformer with a line to neutral feeder, as it does when powered normally by a line-to-line connection 120 degrees out of phase? I’m having some trouble getting consensus on this one.
We put the question to Joe Pottebaum, senior application engineer for Yaskawa Electric America, Inc. He answers:
“To answer this question definitively requires more information than what is given. Nevertheless, if we assume that the auto-transformer is suitably rated for the motor, then the motor will suffer virtually no degradation in its performance when powered through the auto-transformer. The motor will be happy as long as it sees 240 volts. However, there are some considerations.
“Typical household 240 Vac single phase service is grounded at the center-tap of the transformer secondary feeding the building. The grounded center-tap becomes the neutral (white wire) for two 120 Vac circuits throughout the building. Therefore, when 240 Vac is used directly to power a 240 volt motor, the maximum voltage with respect to ground is 120 Vac. In the description, it appears that the auto-transformer is being used to step up or step down voltage from a feeder with one side grounded. If the motor is connected between that grounded side and the auto-transformer 240 Vac tap, then the maximum voltage with respect to ground is 240 Vac, double the 120 Vac from a conventional service. Generally, this is not a problem, but does merit checking with the motor manufacturer.”
Read Who’s using industrial drives? for links to additional motor related topics.
Posted by Ask Control Engineering on February 20, 201
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.