NERC PRC-025: 2019 compliance starts now
Six steps to meet the new Generator Relay Loadability Standard.
- Maximum rated megavolt amperes (MVA) for the generator
- Rated power factor and voltage
- Maximum MVA for generator step up (GSU) and unit auxiliary transformer, and associated impedances
- Rated primary and secondary voltages at the set tap position for the GSU
- Utility voltage
- Megawatts (MW) reported to the transmission planning coordinator