Variable frequency drive cables support large horsepower motors
Belden introduces MCM VFD cables to support large horsepower motors.
Belden, provider of signal transmission solutions for mission-critical applications, announced the extension of its line of variable frequency drive (VFD) cables to include 250 MCM, 350 MCM and 500 MCM sizes. MCM VFD cables support installations of up to 250 horsepower motors at 460 V for use in oil and gas, petrochemical, power generation, water and wastewater treatment and other demanding industrial environments.
Belden MCM VFD cables are rated for use in exposed-run cable trays, direct burial and in wet or dry conditions. Belden’s MCM VFD cables are said to be designed to provide superior performance in noise-sensitive applications or in any damp or wet environment where reflected wave voltages may degrade PVC/nylon conductors. The cable is suitable for use with virtually all variable frequency drives, as well as for use as shielded power cable for other solid-state devices.
Electrical performance, reliability for VFD applications
VFDs reduce facility energy consumption and thus operating costs; however, VFDs can be a significant source of noise, most particularly electromagnetic interface (EMI), in a facility. In addition, VFDs are usually operated in close proximity to sensitive instruments, critical networks and safety systems. Proper cable selection from cables specifically designed to connect to VFDs can mitigate adverse effects on nearby cable systems and reduce the likelihood of cable or motor failure.
The design of Belden’s MCM VFD cables are said to provide superior common mode current protection and help protect a system against damage from reflected wave voltages and capacitively coupled current for maximum safety and reliability. Design features of Belden MCM VFD cables include symmetric bare grounds, dual copper tape shield, enhanced XLP insulation, industrial-grade PVC jackets for longer life and a TC-ER (Exposed Run) rating that allows cable to run from cable tray to point of utilization per the NEC to reduce the need for additional support or protection.
Belden’s MCM VFD cable carries the following ratings: 2000 V UL 1277 Type TC-ER per 2005 NEC Article 336, 1000V CSA TC C22.2 No 230, 90 ⁰C wet/dry, Class I & II, Div. 2 hazardous locations, UL 1685 vertical tray flame test, FT4, IEEE 1202 vertical tray flame test at 70,000 BTU/hour. The cable is rated UL direct burial, oil and sunlight resistant, RoHS compliant and CE approved.
- Edited by Control Engineering, CFE Media
Find other industrial networking products at controleng.com/networks
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.