UPS maintenance bypass cabinet integrates three functions
This UPS bypass cabinet system enables IT and facility managers to integrate power transformation, power distribution and maintenance bypass into a single cabinet. This three-in-one cabinet complements a rack-based 60 kVA UPS parallel system, and is designed to allow the transfer of power to full system bypass to perform service, testing and maintenance on up to a full rack of UPS units without interrupting power to the critical load.
The Powerware BladeUPS Maintenance Bypass Cabinet (MBC) enables IT and facility managers to integrate power transformation, power distribution and maintenance bypass into a single cabinet. This three-in-one cabinet complements a rack-based 60 kVA Powerware BladeUPS parallel system, and is designed to allow the transfer of power to full system bypass to perform service, testing and maintenance on up to a full rack of Powerware BladeUPS without interrupting power to the critical load.
Instead of having a separate power distribution unit or step-down transformer, distribution cabinet and bypass cabinet, this system combines the convenience and simplicity of all three functions in one factory-tested box. The integral maintenance bypass is a mechanical way to bypass the internal components of the UPS while still sending utility power to the load. If the UPS must be repaired internally, it can be completely isolated from utility power and a technician can safely perform service without voltage present.
The unit uses a TP-1 transformer, which meets the U.S. Department of Energy standard for the Energy Star program, to step down utility power from 480 V to 208/120 V to provide electrical isolation and appropriate input voltage for the UPS modules. With high efficiency, even at low loads, the transformer yields significant savings in utility costs.
Additional features include:
• Integrated power distribution with two 42-pole Cutler Hammer panelboards for easy installation of additional breakers in the field
• Multi-function design that integrates electrical isolation, voltage transformation, electrical distribution and maintenance bypass; simplifies the data center architecture and conserves floor space, compared to separate maintenance bypass and power distribution systems
• Free-standing design that harmonizes with other data center equipment and easy installation and use with flexible access and deployment options.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.