# Understanding time current curves: Part 1

## The first installment of a three-part series about time current curves (TCCs) provides a quick overview of item identification and how to read TCC plots.

01/21/2014

A time current curve (TCC) plots the interrupting time of an overcurrent device based on a given current level. These curves are provided by the manufacturers of electrical overcurrent interrupting devices, such as fuses and circuit breakers. These curves are part of the product acceptance testing required by Underwriters Laboratories (UL) and other rating agencies. The shape of the curves is dictated by both the physical construction of the device as well as the settings selected in the case of adjustable circuit breakers. The time current curves of a device are important for engineers to understand because they graphically show the response of the device to various levels overcurrent. The curves allow the power systems engineer to graphically represent the selective coordination of overcurrent devices in an electrical system. Modern power system design software packages, such as EasyPower, SKM Power Tools, and Etap, contain graphical libraries of curves to allow the power system engineer the ability to plot, analyze, and print the curves with minimal effort compared to the previous methods used when coordinating a power system.

TCC item identification

The TCC diagram shown in Figure 1 (below) plots the interrupting response time of a current interrupting device versus time. Current is shown on the horizontal axis using a logarithmic scale and is plotted as amps X 10X. Time is shown on the vertical axis using a logarithmic scale and is plotted in seconds X10X .The light blue curve is a switchgear feeder circuit breaker curve. The violet curve is the switchgear main circuit breaker curve. The red curve is the transformer primary fuse curve. The orange curve is the transformer damage curve. The green curves are the cable damage curves. Each one of these items will be explained. The system represented by this curve is well coordinated and adequately protected from damage. It also has minimal arc flash hazard category ratings due to low instantaneous circuit breaker trip values.

The one line diagram (see Figure 2) and TCC plot show a typical hypothetical industrial power system. There is a utility delivery point with power supplied at a medium voltage level (in this case 4,160 V), which feeds the primary side of a 2.5 MVA power transformer through a medium voltage fused switch containing an E Class fuse. The 480 V secondary side of the transformer feeds a piece of low voltage power switchgear utilizing draw out low voltage power circuit breakers for the main and feeder circuit breakers. The TCC plot also displays the transformer and cable damage curves. These curves are based on accepted industry consensus standards published by the American National Standards Institute (ANSI, for the transformer) and the Insulated Cable Engineers Association (ICEA, for the cables). Interpreting the damage curves is fairly straight forward. Operating conditions (overcurrent protection) must be kept to the left of the damage curve to guarantee no permanent damage is done to the transformer or cable in question. Operating conditions that allow operation to the right of the damage curve subject the device in question to currents that can cause permanent irreversible damage, a shortened lifespan, and possible catastrophic failure. Therefore, the overcurrent and circuit breaker coordination schemes must take this into account during the initial design phase.

There are two transformer damage curves (shown in orange on Figure 1) – one is dashed, the other is solid. The solid damage curve is unbalanced and takes into account a de-rating factor for transformer winding type and fault type. The dashed damage curve is the 100% rating curve with no de-rating consideration. The transformer inrush current is also plotted a single point on the TCC diagram. Again, as part of the initial design, the transformer inrush current must be to the left of the transformer primary fuse curve, otherwise the fuse will open when the transformer is energized. These differences in the unbalanced and 100% damage curves can be mitigated with additional protective relaying to allow the 100% curve to be used for power system design without the risk of transformer damage.

There are three cable damage curves (shown in green on Figure 1). There is one curve for each cable represented on the one line diagram. As part of the initial design, the overcurrent interrupting device must limit the fault current to left of the damage curve to prevent permanent damage. The damage curves for the cables are dependent on size, insulation type and raceway configuration.

This post was written by David Paul. David is a Principle Engineer at MAVERICK Technologies, a leading automation solutions provider offering industrial automation, strategic manufacturing, and enterprise integration services for the process industries. MAVERICK delivers expertise and consulting in a wide variety of areas including industrial automation controls, distributed control systems, manufacturing execution systems, operational strategy, business process optimization and more.

The Top Plant program honors outstanding manufacturing facilities in North America. View the 2015 Top Plant.
The Product of the Year program recognizes products newly released in the manufacturing industries.
The Engineering Leaders Under 40 program identifies and gives recognition to young engineers who...
Prescriptive maintenance; Hannover Messe 2017 recap; Reduce welding errors
Safety standards and electrical test instruments; Product of the Year winners; Easy and safe electrical design
Safer human-robot collaboration; 2017 Maintenance Survey; Digital Training; Converting your lighting system
Mobility as the means to offshore innovation; Preventing another Deepwater Horizon; ROVs as subsea robots; SCADA and the radio spectrum
Future of oil and gas projects; Reservoir models; The importance of SCADA to oil and gas
Big Data and bigger solutions; Tablet technologies; SCADA developments
Automation modernization; Predictive analytics enable open connectivity; System integration success; Automation turns home brewer into brew house
Commissioning electrical systems; Designing emergency and standby generator systems; Paralleling switchgear generator systems
Natural gas for tomorrow's fleets; Colleges and universities moving to CHP; Power and steam and frozen foods

### Annual Salary Survey

Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.

There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.

But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.

Maintenance and reliability tips and best practices from the maintenance and reliability coaches at Allied Reliability Group.
The One Voice for Manufacturing blog reports on federal public policy issues impacting the manufacturing sector. One Voice is a joint effort by the National Tooling and Machining...
The Society for Maintenance and Reliability Professionals an organization devoted...
Join this ongoing discussion of machine guarding topics, including solutions assessments, regulatory compliance, gap analysis...
IMS Research, recently acquired by IHS Inc., is a leading independent supplier of market research and consultancy to the global electronics industry.
Maintenance is not optional in manufacturing. It’s a profit center, driving productivity and uptime while reducing overall repair costs.
The Lachance on CMMS blog is about current maintenance topics. Blogger Paul Lachance is president and chief technology officer for Smartware Group.
Featured articles highlight technologies that enable the Industrial Internet of Things, IIoT-related products and strategies to get data more easily to the user.
Compressed air plays a vital role in most manufacturing plants, and availability of compressed air is crucial to a wide variety of operations.
This digital report will explore several aspects of how IIoT will transform manufacturing in the coming years.
Maintenance Manager; California Oils Corp.
Associate, Electrical Engineering; Wood Harbinger
Control Systems Engineer; Robert Bosch Corp.
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.