Tutorial: Vortex shedding flowmeters
Cost-effective and reliable flowmeter technology retains a high position in process plant toolboxes.
One technology that scored well in our recent Product Research on flowmeters that we have yet to cover here is vortex shedding. This type of device calculates liquid, gas, or steam flow by observing the vortices formed when a fluid stream passes an obstruction with known characteristics.
When a bar (called a bluff body) is inserted across the interior of a pipe, fluid flowing through the pipe has to pass on one side or the other. As it passes, vortices form on both sides of the body. The frequency of these vortices is determined by the velocity of the fluid stream. Instrumentation devices use a detector to count the frequency, such as strain gages, ultrasonic, capacitance, magnetic, or other types of sensors to generate electrical pulses from the liquid vibrations. The transmitter counts these pulses and converts the reading to a stream velocity from which it calculates fluid volume.
This approach has many advantages:
Accuracy and turn-down ratio are sufficient for most general process applications;
Wide range of sizes available;
Durable and not prone to drift;
Stable, so they need little calibration or maintenance;
Good for gas, steam, and liquid;
Most can mount in any position so long as the pipe is full;
No moving parts;
Works with conductive or non-conductive liquids; and
Configuration options include spool or wafer designs, and insertion styles for larger sizes.
However, there are some downsides you should keep in mind:
Any design that introduces an obstruction causes a pressure drop and creates clogging potential. The extent varies between manufacturers;
Solids depositing on the bluff bar can disrupt accurate readings;
Two-phase flows and slurries are not well-suited for this kind of flowmeter;
Over time, the bluff bar’s shape may change from wear which can cause drift;
Liquid viscosity is generally limited to 30 cp;
Specific designs can be dedicated either to gas or liquid, but not both; and
Ensure sufficient up- and down-stream straight pipe to control turbulence.
Some of the more sophisticated designs add sensors for variables such as fluid temperature and pressure. These readings are often very useful, and can be used to calculate a mass flow reading when known fluid characteristics are added.
These discussions are general, so review specifics with your supplier.
Vortex shedding flowmeters are manufactured by many companies, including:
—Peter Welander, process industries editor, PWelander@cfemedia.com ,
Control Engineering Process Instrumentation & Sensors Monthly
Register here and scroll down to select your choice of free eNewsletters .
- Events & Awards
- Magazine Archives
- Oil & Gas Engineering
- Salary Survey
- Digital Reports
Annual Salary Survey
After almost a decade of uncertainty, the confidence of plant floor managers is soaring. Even with a number of challenges and while implementing new technologies, there is a renewed sense of optimism among plant managers about their business and their future.
The respondents to the 2014 Plant Engineering Salary Survey come from throughout the U.S. and serve a variety of industries, but they are uniform in their optimism about manufacturing. This year’s survey found 79% consider manufacturing a secure career. That’s up from 75% in 2013 and significantly higher than the 63% figure when Plant Engineering first started asking that question a decade ago.