Tutorial: Running down interference to improve device performance
EMI and RFI can ruin your sensor data, and trying to trace sources can drive you nuts. There are solutions.
By Control Engineering Staff
In past issues we’ve talked about problems with ground loops and cross talk , and how these can ruin sensor data. Electromagnetic and radio frequency interference (EMI and RFI) can also cause your sensor data to go nuts, and finding its sources can make you do the same. The two types of interference can present similar symptoms, but the nature of their sources and solutions are not the same. Trying to define the differences between the two is a little vague and many people use the two terms interchangeably for all practical purposes.
EMI is broadband electrical noise that typically emanates from wiring and equipment. In any situation where there is heavy inductive load switching, electric motors, and particularly complex devices like VFDs (variable frequency drives), you’ll get EMI. In the same way it hurts your radio reception, noise is transferred to your sensors through inductive and capacitive coupling, often between wires. You can get it from having data cables too close to ac wiring in cable trays, for example, which means laying a thermocouple extension wire next to a 440 Vac line is asking for trouble.
RFI is higher frequency, and generally the tougher problem to fix. While EMI usually moves from cable to cable, RFI can be picked up all sorts of ways. It often comes from radio transmitters such as walkie-talkies, cell phones, CB radios, etc. (A driver triggering a CB radio from his truck while driving past my house nearly blew out my stereo speakers.) You’ve probably heard the characteristic beeping on the phone caused by someone’s Blackberry trying to exchange data. There are anecdotes of radios on barges sending systems haywire as they pass plants on the shore.
The thing that makes such interference hard to eliminate is that it can be intermittent. For example, a welder working in the plant makes the temperature sensors on a vessel change, but then they recover when the welding stops. The potential for damage to the process depends on the EMI severity and how well you’ve deployed suppression techniques. Problems that run all the time, more or less, can be tracked down and fixed. The TC wire and ac cable in the same tray are an example.
Many suppression techniques for both kinds of interference exist:
Keeping critical cables separated;
Use of twisted pair and shielded cables;
Filtering capacitors at strategic points;
Careful grounding where appropriate;
Use of signal isolators;
Appropriate case and enclosure designs;
Selection of devices that are designed to reject interference; and
Many other possibilities.
Going into depth in this context is not practical, but there are application notes from several sources that can help you analyze and solve your interference problems. Here are three links to get you started:
These companies can suggest specific practices and offer devices to make the task easier. Also, Control Engineering has offered more extensive discussions on related topics:
Drive EMI: How to control high-frequency noise of adjustable speed drives (ASDs)
Silence of the Drives
Who Puts the 'Industrial’ in Ethernet?
—Peter Welander, process industries editor, PWelander@cfemedia.com ,
Control Engineering Process Instrumentation & Sensors Monthly
Register here to select your choice of free eNewsletters .
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.