Time-proportional control: more from an on/off switch
Time-proportional control, a form of pulse-width modulation, is a mathematical technique that allows a feedback controller to use an on/off or discrete actuator as if it were a continuous actuator capable of generating control efforts anywhere between 0% and 100%. The trick is to turn the actuator on and off for periods proportional to the desired control effort.
Time-proportional control , a form of pulse-width modulation , is a mathematical technique that allows a feedback controller to use an on/off or discrete actuator as if it were a continuous actuator capable of generating control efforts anywhere between 0% and 100%. The trick is to turn the actuator on and off for periods proportional to the desired control effort.
Consider a home cooling system, for example. Most thermostats use a “bang-bang” control algorithm that compares the actual room temperature with the setpoint specified by the room’s occupants, then turns the air conditioner fully on or fully off if the temperature is more than a few degrees too high or too low. This technique causes the room temperature to fluctuate around the setpoint, but in most homes, that’s good enough.
By cycling a discrete actuator on and off, a time-proportional controller can emulate the effects of a continuous actuator. In teh top example, the controller is attempting to achieve a 50% control effort by keeping the actuator in the "on" position 50% of the time.
The thermostat could achieve tighter control with a continuous actuator such as a motorized damper that would continuously allow a measured amount of chilled air into the room. Those are common in commercial HVAC applications but are typically too expensive for home use.
But with time-proportional control, a home thermostat wouldn’t need a continuous actuator to emulate its effects. It could use the air conditioner’s on/off switch to regulate not the amount of cool air being dumped into the room but the duration of each blast. To achieve an X% control effort, the thermostat would simply turn the air conditioner on for X units of time then off for 100 minus X units of time.
If those units are small compared to the time it takes to cool the room (a few minutes or so), then the average effect of turning the air conditioner fully on for X% of the time will be identical to running the air conditioner at X% of full capacity continuously. In the short term, the room temperature would still fluctuate around the setpoint, but typically not as much as with bang-bang control.
Other applications of time-proportional control might require minimizing those fluctuations, in which case the minimum time between “on” and “off” commands — the controller’s duty cycle — would have to be reduced. Unfortunately, that would also increase the wear and tear on the actuator by increasing the frequency with which it switches states.
A 50% control effort would be the worst case since the actuator would have to switch states at the end of every duty cycle. In the home cooling example, a duty cycle less than several minutes long would quickly wear out the air conditioner’s motor starter.
At the other extreme, a duty cycle on the order of hours would help extend the life of the motor starter, but the air conditioner would end up running for hours on end, thereby amplifying the room temperature’s fluctuations to an uncomfortable degree.
Time-proportional control works best on relatively slow processes and processes that provide a mechanism for smoothing out the effects of the actuator’s flip-flopping. In addition to temperature control, applications suitable for this technique include level and pressure control of large volumes and applications for which a continuous actuator would be prohibitively expensive.
Vance VanDoren is consulting editor for Control Engineering . Reach him at firstname.lastname@example.org .
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.