Steam tip: Ensure that your boiler is operating at its best performance
There are many things you can do to ensure your boiler is operating optimally.
There are many things you can do to ensure your boiler is operating optimally. Listed below are a few tips to consider:
- Always run the boiler at its rated pressure.
- Do not run the boiler above its rated output. For consistency, steam boilers are rated to evaporate steam at atmospheric pressure and with a feedwater temperature of 212 F. If the boiler pressure is higher and the feedwater temperature is lower (which is always the case), then the boiler’s actual maximum output will be less than its rated output, typically derated by about 6% to 7%. You might see the boiler rated in terms of 11,025 lbs/hr. ‘From and At’ or ‘F & A’. Its maximum continuous rating will always be less.
- If designing a new steam system, ensure that the highest practical pressure is used to distribute the steam, and choose a boiler that operates at the same pressure.
- Keep the TDS of the boiler water within recommended limits. This can only be achieved realistically by automatic blowdown systems.
- Monitor the boiler water TDS and chemical constituency regularly to ensure the boiler water treatment is correct.
- Maintain the boiler feedwater at the highest practical temperature.
- Return as much condensate as possible from the plant to the feedtank.
- Ensure you recover heat from the TDS blowdown to feedtank.
Content provided by Spirax Sarco, originally published in Steam News Magazine.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.