Significant changes to the commercial provisions in 2012 IECC
Except for climate zones 1 through 3, a continuous air barrier is required around the thermal building envelope (C402.4). Subsection C402.4.1.1 details the construction requirements of the air barrier and subsection C402.4.1.2 lists three compliance options, one of which is required to be met: materials, assemblies, or full building testing (see Figure 3). A table of maximum fenestration assembly leakage rates is provided in Section C402.4.3.
Unless required to comply with IBC Section 715 or 715.4 or UL 1784, doors and access openings from conditioned spaces into shafts, chutes, stairways, and elevator lobbies shall meet the fenestration requirements or be sealed per a newly added section (C402.4.4). Stairway, shaft, and outdoor air intakes and exhausts shall be provided with motorized dampers limited to a leakage rate of 4 cfm/sq ft. Gravity dampers meeting a 20 cfm/sq ft leakage rate are permitted as an exception for outdoor intakes and exhausts in climate zones 1 to 3, buildings less than 3 stories, as exhaust and relief dampers, and where the design outdoor air intake or exhaust capacity is ≤ 300 cfm. Dampers smaller than 2 ft in either dimension are permitted a leakage rate of 40 cfm/sq ft (C402.4.5).
Exposed outdoor piping insulation must now be protected from degradation, and use of adhesive tapes is not permitted (C403.2.8.1). Some exceptions to piping insulation requirements (C403.2.8) were also modified. The temperature range in exception 3 was decreased from 55 to 105 F to 60 to 105 F. Exception 5 no longer applies to piping 4 ft or less in length but instead to strainers, control valves, and balancing valves on piping with a diameter of 1 in. or less. Exception 6 was added that applies to buried piping conveying fluids ≤ 60 F.
Table C403.2.8, Minimum Pipe Insulation Thickness, was expanded, and the insulation thicknesses for very hot fluids and steam were increased tremendously; however, a footnote was added allowing a thickness reduction for direct-buried heating and hot water system piping. An exception was added to Section C404.5, Pipe Insulation, for heat-traced piping systems, specifying that they must meet the insulation thickness requirements per the manufacturer’s installation instructions.
A minimum insulation of R-3.5 is now required for radiant panels, associated U-bends and headers, and the bottom surfaces of structures incorporating radiant heating (C402.2.8).
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.