Significant changes to the commercial provisions in 2012 IECC
Except for climate zones 1 through 3, a continuous air barrier is required around the thermal building envelope (C402.4). Subsection C402.4.1.1 details the construction requirements of the air barrier and subsection C402.4.1.2 lists three compliance options, one of which is required to be met: materials, assemblies, or full building testing (see Figure 3). A table of maximum fenestration assembly leakage rates is provided in Section C402.4.3.
Unless required to comply with IBC Section 715 or 715.4 or UL 1784, doors and access openings from conditioned spaces into shafts, chutes, stairways, and elevator lobbies shall meet the fenestration requirements or be sealed per a newly added section (C402.4.4). Stairway, shaft, and outdoor air intakes and exhausts shall be provided with motorized dampers limited to a leakage rate of 4 cfm/sq ft. Gravity dampers meeting a 20 cfm/sq ft leakage rate are permitted as an exception for outdoor intakes and exhausts in climate zones 1 to 3, buildings less than 3 stories, as exhaust and relief dampers, and where the design outdoor air intake or exhaust capacity is ≤ 300 cfm. Dampers smaller than 2 ft in either dimension are permitted a leakage rate of 40 cfm/sq ft (C402.4.5).
Exposed outdoor piping insulation must now be protected from degradation, and use of adhesive tapes is not permitted (C403.2.8.1). Some exceptions to piping insulation requirements (C403.2.8) were also modified. The temperature range in exception 3 was decreased from 55 to 105 F to 60 to 105 F. Exception 5 no longer applies to piping 4 ft or less in length but instead to strainers, control valves, and balancing valves on piping with a diameter of 1 in. or less. Exception 6 was added that applies to buried piping conveying fluids ≤ 60 F.
Table C403.2.8, Minimum Pipe Insulation Thickness, was expanded, and the insulation thicknesses for very hot fluids and steam were increased tremendously; however, a footnote was added allowing a thickness reduction for direct-buried heating and hot water system piping. An exception was added to Section C404.5, Pipe Insulation, for heat-traced piping systems, specifying that they must meet the insulation thickness requirements per the manufacturer’s installation instructions.
A minimum insulation of R-3.5 is now required for radiant panels, associated U-bends and headers, and the bottom surfaces of structures incorporating radiant heating (C402.2.8).
- Events & Awards
- Magazine Archives
- Oil & Gas Engineering
- Salary Survey
- Digital Reports
- Survey Prize Winners
Annual Salary Survey
Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.
There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.
But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.
Read more: 2015 Salary Survey