Remotely resettable electronic circuit breaker
The E-T-A ESX10-TC is a 12 V DC version of the 24 V ESX10-T and is designed for SCADA/RTU applications, providing protection for switch-mode power supplies and solar/battery-based systems.
E-T-A expanded its line of electronic circuit protection products with the ESX10-TC, a 12 V dc version of the ESX10-T, 24 V dc product offering and is designed for SCADA/RTU applications – providing protection for 12 V dc switch-mode power supplies and solar/battery based systems.
The most unique feature of ESX10-TC, E-T-A said, is the ability to remotely reset the device from outside an enclosure. This can be accomplished via a simple momentary push button or from an output of an RTU or PLC controller. In RTU/SCADA applications, equipment is primarily located in remote unpopulated locations. The remote reset functionality reduces the need for field engineers to travel to sites to troubleshoot equipment – reducing the overall cost of equipment maintenance and downtime.
The ESX10-TC is available in fixed current ratings from 1 A to 10 A and provides selective load protection - ensuring exclusive disconnection of the current path in the event of an overload or short circuit in the field load device without compromising the dc 12 V power source (such as battery drain).
The ESX10-TC limits the short circuit current to 1.3 to 1.8 times rated current and disconnects 100 ms after the fault has been detected. Inrush peaks are tolerated from capacitive loads of more than 20,000 μF and is designed with an auxiliary output to provide individual alarm capabilities for critical process flow applications. This space-saving device has a width of only 12.5 mm and 80 mm in height and depth. Its low power consumption makes it ideally suited for battery-buffered dc 12 V applications, specifically in the solar industry.
The ESX10-TC is DIN rail ready and can be mounted either individually or in a group side-by-side with a simplistic bus bar system for +12 V dc and ground. It also uses the same screw terminals as its 24 V dc counterpart which allows up to a 10 mm² conductor to be wired directly to the device, this ensures reliable and safe wiring connections.
- Edited by Chris Vavra, Control Engineering, www.controleng.com
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.