Relays Bridge the Gap in Causeway's Power-Protection Plan
The 24-mi. Lake Ponchartrain Causeway provides a vital link between New Orleans and communities to its north. In addition to serving some 30,000 vehicles on any typical workday, it also is a primary evacuation route for coastal areas in the event of hurricanes and other severe storms. When modernizing the twin-span's infrastructure, the Greater New Orleans Expressway Commission recognized the n...
The 24-mi. Lake Ponchartrain Causeway provides a vital link between New Orleans and communities to its north. In addition to serving some 30,000 vehicles on any typical workday, it also is a primary evacuation route for coastal areas in the event of hurricanes and other severe storms. When modernizing the twin-span's infrastructure, the Greater New Orleans Expressway Commission recognized the need for a redundant power design incorporating the latest power-control capabilities.
The causeway's high-voltage system serves drawbridge operations, cell-phone towers, toll facilities and a series of variable-message warning signs that alert drivers during frequent fog conditions and other emergency situations. Engineers at Baton Rouge, La.-based Gulf Engineers and Consultants designed an automated distribution system to meet causeway needs.
The system is capable of automatic fault detection, isolation and restoration, with communications over fiber-optic cable. It includes 11 resettable fault-interrupting switches rated 275-kV, 600-amp continuous, installed every two miles in a loop plan. A three-way switch is located mid-span as a tie point, which is normally open. Power sufficient to support the entire causeway is available from either of the utility's serving the span's endpoints in the case that either utility experiences an outage. In the event of a fault between a sectionalizing switch and a load, the plan uses a resettable fault interrupter (RFI) to isolate the faulted cable section. If a fault occurs between two sectionalizing switches on the main cable, one of the shore-based switches isolates the bridge from the main power source, and then reconfigures the system and restores power to the isolated segment by feeding from the alternate source.
When selecting relays for the project, engineers were looking for flexible, programmable units, because designers knew they would need to create a customized database that could be spread across the entire bridge locally, rather than being centralized in a single location. The devices chosen incorporate patented technology that allows high-speed, point-to-point communication of relay contact status, and high-speed bus protection, sectionalizing, restoration and interlock schemes.
The relays were programmed using the manufacturer's proprietary software. Design specifications require power restoration within 30 seconds. If one of the two endpoint utilities goes down, the shore switch at that service end has to open and the midpoint tie switch has to close to allow the other utility to supply the bridge's entire needs. If the system isolates a fault on the bridge—whether in a current transformer bus, cable or switch—it is re-energized from the tie point back to where the fault has been isolated.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.