Priming the pump
Problem: Pumps with large-volume suction lines that run above the fluid level are often difficult to prime.
Problem: Pumps with large-volume suction lines that run above the fluid level are often difficult to prime. The problem results from the large amount of air that must run through the pump, plus the requirement to lift the fluid from the reservoir into the suction line. Simply filling the pump with fluid is not enough, and the suction line cannot be filled because it drains back into the reservoir. A foot valve is often undesirable or unavailable. Is there another way around this problem?
Solution: Install a port (1/4-in. pipe) at the highest point on the suction line, and attach a small venturi with plant air flowing through it. Open the valve in the pipe. Air flowing through the venturi creates a vacuum at the highest point and draws the fluid into the line until all air is evacuated. At this point, fluid begins to flow out the hose attached to the venturi exhaust, along with plant air. Close the valve in the pipe. The suction line and pump are now full of fluid. Compressed air is disconnected from the venturi, and the pump started.
Contributor: John R. Giegel, PE, Plant Mechanical Engineer, Werner Co., Greenville, PA; 724-588-2000 x 2439
Annual Salary Survey
After almost a decade of uncertainty, the confidence of plant floor managers is soaring. Even with a number of challenges and while implementing new technologies, there is a renewed sense of optimism among plant managers about their business and their future.
The respondents to the 2014 Plant Engineering Salary Survey come from throughout the U.S. and serve a variety of industries, but they are uniform in their optimism about manufacturing. This year’s survey found 79% consider manufacturing a secure career. That’s up from 75% in 2013 and significantly higher than the 63% figure when Plant Engineering first started asking that question a decade ago.