Power Supply Selection
Tips and Tricks: When selecting your next ac-dc industrial power supply, don’t overlook these five important considerations, including hours of operation and...
The use of power supplies for industrial and control applications requires careful consideration of the operating conditions, environment, and power loads. Here is a listing of some frequently overlooked considerations when selecting ac-dc power supplies. Included are links to more information on each topic.
1. Hours of operation: Sometimes a low-cost power supply is selected for applications that require 24/7 operation. This is penny-wise and pound-foolish since the construction of low-cost supplies employ low-cost components (capacitors, active components, fans, etc.) that are unsuited for constant operation. The best solution for 24/7 applications is to find an industrial-rated power supply that includes a 5-year or longer warranty. The “warranty period” is a good indication of the type of components used in power-supply construction.
2. Peak power loads: Many times industrial and control equipment includes dc motors, solenoids, pumps, etc. These types of loads typically have a peak start-up current that exceeds their steady state current. The system designer can either select a power supply that handles the peak current or consider a lower cost solution by employing a peak-rated power supply.
3. Ambient temperatures: One of the biggest killers of power supplies is “heat.” Since all power supplies generate heat due to their inherent inefficiencies, they require cooling by conduction via heat sinks, natural air convection, forced air-cooling, or a combination of all three. However, whichever cooling method is employed, due consideration to the prevailing ambient air temperature range must be included in the end equipment design.
4. Corrosive or dusty environments: When fan-cooled power supplies are employed in corrosive or dusty environments, a scheduled maintenance program must be established to periodically clean air filters and replace fans because their bearings will wear out quickly under these conditions. In these environments, it would be wise to consider non-fan cooled power supplies that are cooled via conduction or natural airflow (without fans).
5. AC line noise: Most ac-dc power supplies include electromagnetic (EMI) filters. These embedded EMI filters serve to protect the ac line from noise generated by the supply as well as to protect the supply from noise generated by other devices connected to the ac line. There are applications where the ac line noise is so extreme that additional EMI filtering is required. In these cases, it is wise to add an external EMI filter before the ac input to the power supply. Many power supply manufacturers can assist the end user in the selection of an appropriate external EMI filter.
- Mel Berman is product marketing manager, TDK-Lambda Americas; edited by Mark T. Hoske, content manager CFE Media, Control Engineering, Plant Engineering, and Consulting-Specifying Engineer, mhoske(at)cfemedia.com.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.