Portland Community College Newberg Center
New construction: Portland Community College Newberg Center; Interface Engineering Inc.
Location: Newberg, Ore.
Firm name: Interface Engineering Inc.
Project type, building type: New construction, school (college, university)
Project duration: 1.5 years
Project completion date: Aug. 31, 2007
Project budget for mechanical, electrical, plumbing, fire protection engineering only: $194,000
The new Education Center at PCC Newberg will be the first higher education building in Oregon—and one of the first in the nation—to become net-zero and U.S. Green Building Council LEED Platinum certified. Achieving these lofty goals was the central challenge for the design team. Identifying the most cost-effective sustainable strategies suitable to the site while reducing energy use to 60%-70% less than a conventional code building without sacrificing comfort or building aesthetics was a daunting task.
To achieve these lofty goals, Interface designed and implemented numerous sustainable features, including a highly insulated building envelope; passive heating/cooling systems; digital, addressable lighting control systems; and rooftop solar panels. The design team also improved insulation by incorporating structural insulations panels (SIP) for the roof and exterior walls. These provide less thermal breaks and more even temperatures throughout the facility, reducing heating and cooling loads. A majority of the building is cooled by natural ventilation only with a combination of exterior louvers that bring fresh air in, stacks along the building’s spine that push hot air out, and ceiling fans throughout the facility. When outside temperatures are below 55 F, a heat recovery ventilation (HRV) system kicks in. It brings in fresh outside air and warms it with heat recovery wheels that recover most of the building heat normally rejected to the outside. A radiant slab, with 90-F water running through it, heats the building to 68 F. Daylighting controls are in the classroom, administrative, multipurpose, and common spaces. Combined with the skylights and windows, the design effectively maximizes the use of natural daylight while also reducing required electrical lighting and lowering the energy use by 15%. The skylights are equipped with motorized louvers that track the sun, allowing the appropriate amount of daylight into the room.
Classrooms have manual controls to drive the louvers to a closed position to accommodate audiovisual presentations. Additional energy reduction features include: domestic hot water heat pump, a significant efficiency improvement over a standard electric hot water heater; solar preheating of ventilation air to reduce heating energy; low-flow bathroom fixtures and hand dryers that use one-tenth of the energy of paper towels; laptop computers in the computer lab space to reduce plug loads; high efficiency T5 bulbs for all interior light fixtures; improved glazing performance; and overall water use reduced by 49.2% through the use of low-flow faucets and toilets.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.