NERC issues reliability advisories on February Florida outage
The North American Electric Reliability Corp. announced that analysis of a Feb. 26, 2008, category four system disturbance in Florida has led to the release of three industry-wide reliability advisories.
The analysis of a Feb. 26, 2008, category four system disturbance in Florida has led to the release of three industry-wide reliability advisories, announced the North American Electric Reliability Corporation (NERC) on June 26. The advisories follow the recent release of an interim report on the outage by the Florida Reliability Coordinating Council (FRCC), which contains a number of recommendations to users, owners, and operators of the bulk power system in Florida aimed at preventing recurrence and improving system response to all disturbances.
The first of the three advisories deals directly with the root cause of the outage, a decision to disable key protective relays in a substation west of Miami while troubleshooting was underway. The advisory encourages the industry to review practices and procedures to ensure that proper authorizations are obtained before such measures are taken.
The remaining advisories focus on the capabilities of generation plants to ride through changes in voltage or frequency on the system without unexpectedly disconnecting from the grid, while still protecting generating equipment from permanent damage. They also include provisions to help grid operators and planners better understand and account for generators that may disconnect from the grid during a severe disturbance.
“Every system disturbance is an opportunity to learn more about how the system responds to extreme conditions,” said Robert Cummings, NERC director of events analysis and information exchange. “This event has brought to light a few key issues about the behavior of the system that the entire industry can use to improve the bulk power system’s response to future disturbances.”
Although most of the affected customers were restored within one hour of the initiating events, the Florida outage was ranked a four on NERC’s system event classification scale for the loss of roughly 4,500 MW of customer load, 4,300 MW of generation, and 26 transmission lines. NERC’s event classification scale has five levels and is designed to designate the severity of bulk power system disturbances; category five is the most severe on this scale. Three other events have been ranked a four or higher in the past year out of 33 tracked bulk power system disturbances.
“Our focus is on ensuring the reliability of the bulk power system in North America and putting the standards in place that will eventually reduce the likelihood and severity of future system disturbances,” said Rick Sergel, President & CEO of NERC. “Unfortunately, no standards or enforcement process can prevent all system disturbances from occurring. Issues like severe weather, simultaneous multiple equipment failure and human error can occur, but it’s our job to minimize their effects. Today’s (June 26) advisories will help to do just that.”
The advisories are available on NERC’s website .
Read the June CSE feature on preparing healthcare facilities for long-term outages:
Register for the CSE July 24 Webcast: “The great blackout of 2003: What have we learning?”
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.