Motor protection delivers reliable, efficient operation
Benefits of using a VFD
- Energy savings
- Reduces peak energy demand
- Reduces power when not required
- Fully adjustable speed (pumps, conveyors, and fans)
- Controlled starting, stopping, and acceleration
- Dynamic torque control
- Provides smooth motion for applications such as elevators and escalators
- Maintains speed of equipment, making drives ideal for manufacturing equipment and industrial equipment such as mixers, grinders, and crushers
- Self-diagnostics and communications
- Advanced overload protection
- PLC-like functionality and software programming
- Digital inputs/outputs (DI/DO)
- Analog inputs/outputs (AI/AO)
- Relay outputs
VFDs offer the greatest energy savings for fans and pumps. The adjustable flow method changes the flow curve and drastically reduces power requirements. Centrifugal equipment (fans, pumps, and compressors) follow a general set of speed affinity laws. The affinity laws define the relationship between speed and a set of variables:
Based on the affinity laws, flow changes linearly with speed while pressure is proportional to the square of speed. The power required is proportional to the cube of the speed. The latter is most important, because if the motor speed drops, the power drops by the cube.
Figure 4. Affinity Laws – Flow/Speed
Figure 5. Affinity Laws – Pressure/Speed
Figure 6. Affinity Laws – Power/Speed
Therefore, the power required to operate the fan at 80% speed is half the rated power.
Selecting the correct equipment
Choosing a soft starter or a variable frequency drive often depends on your application. Soft starters are smaller and less expensive when compared with VFDs in larger horsepower applications. Larger VFDs take up more space and are usually more expensive than soft starters.
That being said, while a VFD is often more expensive up front, it can provide energy savings of up to 50%, thereby producing more cost savings over the life of the equipment.
Speed control is another advantage of a VFD, because it offers consistent acceleration time throughout the entire operating cycle of the motor, not just during start-up. VFDs can also provide more robust functionality than soft starters offer, including digital diagnostic information.
It is important to note that a VFD can initially cost two to three times more than a soft starter. Therefore, if constant acceleration and torque control is not necessary, and your application requires current limiting only during start-up, a soft starter may be a better solution from a cost standpoint.
Robert Fenton is a product line manager at Eaton.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.