Modeling natural ventilation
Energy modeling for LEED submission was done on a recent project in which natural ventilation and a radiant floor cooling system were proposed for the dining area of a food court in a local university in Southern California.
Energy modeling for U.S. Green Building Council LEED submission was done on a recent project in which natural ventilation and a radiant floor cooling system were proposed for the dining area of a food court in a local university in Southern California. EQuest was used because it was the most appropriate software at the time, but its developers did not envision such a building, so “workarounds” had to be created to mimic the actual energy use of the building.
Because the design incorporated a mixed-mode approach, and none of the currently available engines allows for multiple systems serving the same space, it was necessary to create the radiant systems as serving “dummy” zones with simulated cooling coils served by fans with 0.0001 kW/cfm energy (because zeroing out fan energy in EQuest can cause instability). Furthermore, it was necessary to perform a dynamic heat transfer analysis in an alternate program to represent a schedule of operation to represent when the natural ventilation was active (in the typical meteorological year file) and when the air conditioning units had to be scheduled to be on for the primary zone.
As shown in Figure 3, there is no way graphically to represent the systems based on the available components in the Schematic Design Wizard. However, with the detailed modules of EQuest and a substantial amount of review of the *.sim files, it was possible to get a reasonably good representation of the energy performance. This was an improvement on the manipulation of baseboard heating modules to simulate radiant floor heating and allowed the computation of cooling energy. While EQuest does have a natural ventilation capability, the complexity of changeover systems for mixed mode approaches did require the heavier manual manipulation of files to represent all of the energy components adequately and meet the expectations of the LEED reviewer panel.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.