Missouri University of Science and Technology (MS+T) Campus Geothermal Energy System
Existing sytem retrofit; Missouri University of Science & Technology (MS&T) Campus Geothermal Energy System; McClure Engineering
Engineering firm: McClure Engineering
2013 MEP Giants rank: 95
Project: Missouri University of Science & Technology (MS&T) Campus Geothermal Energy System
Address: Rolla, Mo., United States
Building type: School (college, university)
Project type: Other
Engineering services: Automation & Controls, Code Compliance, Cx/Retro-Cx, Electrical/Power, HVAC
Project timeline: October 2010 to June 2014
Engineering services budget: $2.5 million
MEP budget: $2.5 million
The first challenge faced by McClure Engineering was choosing the type of system to best suit the campus's heating and cooling needs, as well as its desire for energy efficiency, minimal carbon footprint, and reduced energy costs. To find the best solution, McClure created an hour-by-hour energy model of the campus and modeled various options. The model was compared to metered data to verify its accuracy.
The project includes removing the old steam system and connecting 15 campus buildings to three central heating systems. The challenge was the conversion of all of the existing buildings to the new heating system (a low-temperature, 120 F system) as they were originally designed with other operating parameters. Because each building is unique, McClure examined them individually (on paper and on-site) to determine the optimal ways to make the systems work together.
McClure is currently facing the ongoing challenge of phasing the construction of the entire project, which includes work in existing buildings, construction of new heating/cooling plants, and miles of geothermal piping. Complications include coordinating the work of several subcontractors, minimizing the disruptions to the campus and building occupants, weather delays, and supplying heating and cooling to as much of the campus as possible while installations are completed.
The ground source heat pump system was chosen for its ability to store rejected heat in the ground during the summer and use that heat for building heating during the winter. A unique feature of this design was the decision to utilize a hybrid system (with gas-fired boilers and existing electric chillers to shave the peak loads), which greatly reduced the number of wells required, enabled the project to fit within the university's budget, and provided redundancy in both the heating and cooling systems.
For heating, in many cases the best solution was to replace the coils in air handlers and terminal units in the buildings to work with the new, low-temperature heating system. This allowed the design to maintain high water temperature differentials, thus keeping flows and pump horsepower to a minimum in the buildings and plants.
McClure works closely with the construction manager (JE Dunn), the scheduler (CCS Group), and the school (Missouri University of Science & Technology) to keep the project on schedule and the occupants comfortable through constant communication with all parties. The project team is utilizing a variety of project management tools (including iPads) to facilitate collaboration, effectiveness, and efficiency.
See a presentation from McClure Engineers here.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.