# Managing risks, benefits with closed transition transfer switches

01/06/2014

Passive synchronizing systems

Closed transition transfer switches have successfully used passive synchronizing systems in many applications. Transfer switches use a sync check function for initiating closure to the oncoming source when the two sources are in phase. There are two basic algorithms used by sync check systems: a permissive window algorithm and a predictive algorithm.

A permissive window algorithm is commonly used in both active and passive synchronizing systems. The sync check system measures the voltage, frequency, and phase difference between the two sources. When the three parameters are within some predefined limits, the sources are said to be within a “permissive window.” When the sources have been in the permissive window for some preset period of time, the controller closes to the oncoming source. The required time in the permissive window is typically set to 0.1 to 0.2 seconds for passive synchronizing systems and 0.5 seconds for active synchronizing systems.

A predictive algorithm operates similar to a sync check system except that rather than waiting for the two sources to be in a permissive window for some period of time, it measures the rate of change of the phase angle difference between the two sources and calculates an “optimum phase angle” at which to initiate closure so that at the instant the switch closes, the two sources are as close to in-phase as possible.

Both types of algorithms have been used successfully. Generally speaking, the permissive window algorithm is more robust because the predictive algorithm is susceptible to transients on the voltage sources, which could skew the calculation of the optimum phase angle.

In many applications a slight frequency difference known as a “slip frequency” is imposed between the sources to make sure that they will come into sync with each other at a controlled rate. A slip frequency of 0.1 Hz has been used effectively.

Active synchronizing

Active synchronizing is the process of adjusting the generators’ engine governor to bring the waveform into phase with the utility waveform. Many synchronizing systems also include a voltage matching function, in which the generator sets will adjust the voltage regulator to drive the generator voltage level to match the utility voltage level. The voltage matching function is important in applications where the voltage on the utility transformer varies with load.

Figure 3 represents a generator waveform coming into phase with a utility waveform using an active synchronizer with voltage matching. Note that the utility waveform is constant and the synchronizer drives the generator set waveform in to sync with the utility. The voltage matching function forces the generator voltage to be at the same level as the utility voltage.

The synchronizer will hold the generator in sync with the utility until the synchronizer is turned off, unless a sudden load change causes a frequency change. Load changes on a system bus cause a sudden change in phase angle difference as frequency surges or sags in response to the load transient. This can cause the two sources to momentarily be out of sync until the synchronizer forces them back into synchronization. This is why for systems with multiple closed transition transfer switches, best practice is to allow only one switch to transfer at a time. With an active-phase lock-loop synchronizer, the time to synchronize is relatively short and reliable, so timing between switch operations need not be long.

Transfer and retransfer inhibit

It is common for changes in load on a generator set to cause sudden changes in the voltage and in the phase angle relationship between two sources that have been synchronized. For this reason the possibility of load transients at the moment of transfer should be minimized. For systems with multiple transfer switches, best practice is to allow only one switch to transfer at a time. This can best be achieved either by staggering transfer time delays or by using the transfer and retransfer inhibit functions.

The inhibit functions are used to prevent transfer to either the emergency source (transfer inhibit) or the normal source (retransfer inhibit). When transferring loads with closed transition transfer switches, only one transfer switch should be allowed to transfer at any given time.

The inhibit function can be controlled by a master control used in conjunction with a paralleling system. All switches initially are inhibited from transferring and the master releases the inhibit on one switch at a time.

In simple applications one switch can inhibit another. For example, consider the system in Figure 4 consisting of two closed transition transfer switches. The normally closed aux contact from the normal side of the automatic transfer switch (ATS) 1 is wired into the retransfer inhibit input ATS 2. This will inhibit ATS 2 from beginning its retransfer sequence (including all time delays) until after ATS 1 has transferred back to the normal source.

This configuration does create a potential failure mode. If the first switch fails to transfer or if the aux contact fails, the second switch will not transfer without manual intervention. For this reason it is preferable in some cases to use staggered time delays to prevent the switches from transferring at the same time. As these time delays are typically set on-site, it is important to clearly specify the time delays in commissioning documentation.

It should also be noted that the inhibit function is only required when transferring between two live sources. It is not a requirement in the event of a utility failure, so there is no need to be concerned about not getting the emergency source online quickly enough.

Breaker shunt-trip

Many utilities require that closed transition transfer switches provide means to shunt-trip the breaker on the normal (utility) side of the transfer switch if there is a failure of the transfer switch that causes the two sources to remain paralleled in excess of 100 msec. Many transfer switches have a “fail to disconnect” output which can be used for this. It is up to the installer to connect these devices to the shunt trip of the breaker. Some utilities require maximum parallel timer and lockout relays that are separate from the transfer switch control to implement this function.

Regardless of whether this is required by the local utility, it is considered a best practice to use this function to make sure that two sources are not unintentionally paralleled for an extended period of time. Tripping either the normal side or emergency side breaker will provide the same level of equipment protection, although many utilities require tripping the normal side breaker.

Recommendations

Closed transition transfer switches allow for transferring loads without interruption during a test or when returning to the utility after an outage. This is a significant benefit in some applications; however, there are risks associated with closed transition transfer as two live sources are connected together. For loads that are not protected by a UPS, it is worth considering if the value of not having an interruption during a test or a retransfer to the utility justifies the risk of a closed transition transfer.

There are several methods for mitigating the risk of closed transition transfer:

• Make sure that breakers, transfer switches, and cable are sized to handle the surge current that may result from sources being a few degrees out-of-phase at closure as allowed by the sync check system.
• Consider using active synchronizing with voltage matching to minimize the phase and voltage differences between sources.
• Minimize the possibility of transient conditions at the moment of transfer by inhibiting multiple transfer switches from transferring at the same time and preventing other loads from cycling during the transition.
• Use a transfer switch “fail to disconnect” or maximum parallel timer relay to shunt-trip a feeder breaker to prevent extended paralleling in the event that a transfer switch fails.

Rich Scroggins is a technical specialist in the application engineering group at Cummins Power Generation. Scroggins has been with Cummins for 18 years in a variety of engineering and product management roles. He has led product development and application work with transfer switches, switchgear controls, and networking and remote monitoring products, and has developed and conducted seminars and sales and service training internationally on several products. Rich received his BSEE from the University of Minnesota and an MBA from the University of St. Thomas.

<< First < Previous 1 2 Next > Last >>

The Top Plant program honors outstanding manufacturing facilities in North America. View the 2015 Top Plant.
The Product of the Year program recognizes products newly released in the manufacturing industries.
Each year, a panel of Control Engineering and Plant Engineering editors and industry expert judges select the System Integrator of the Year Award winners in three categories.
2017 Lubrication Guide; Software tools; Microgrids and energy strategies; Use robots effectively
Prescriptive maintenance; Hannover Messe 2017 recap; Reduce welding errors
Safety standards and electrical test instruments; Product of the Year winners; Easy and safe electrical design
Infrastructure for natural gas expansion; Artificial lift methods; Disruptive technology and fugitive gas emissions
Mobility as the means to offshore innovation; Preventing another Deepwater Horizon; ROVs as subsea robots; SCADA and the radio spectrum
Future of oil and gas projects; Reservoir models; The importance of SCADA to oil and gas
Diagnostic functions for system safety; Specifying industrial enclosures; Effective decision support for a crisis
Transformers; Electrical system design; Selecting and sizing transformers; Grounded and ungrounded system design, Paralleling generator systems
Natural gas for tomorrow's fleets; Colleges and universities moving to CHP; Power and steam and frozen foods

### Annual Salary Survey

Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.

There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.

But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.

Maintenance and reliability tips and best practices from the maintenance and reliability coaches at Allied Reliability Group.
The One Voice for Manufacturing blog reports on federal public policy issues impacting the manufacturing sector. One Voice is a joint effort by the National Tooling and Machining...
The Society for Maintenance and Reliability Professionals an organization devoted...
Join this ongoing discussion of machine guarding topics, including solutions assessments, regulatory compliance, gap analysis...
IMS Research, recently acquired by IHS Inc., is a leading independent supplier of market research and consultancy to the global electronics industry.
Maintenance is not optional in manufacturing. It’s a profit center, driving productivity and uptime while reducing overall repair costs.
The Lachance on CMMS blog is about current maintenance topics. Blogger Paul Lachance is president and chief technology officer for Smartware Group.
The maintenance journey has been a long, slow trek for most manufacturers and has gone from preventive maintenance to predictive maintenance.
Featured articles highlight technologies that enable the Industrial Internet of Things, IIoT-related products and strategies to get data more easily to the user.
This digital report will explore several aspects of how IIoT will transform manufacturing in the coming years.
Maintenance Manager; California Oils Corp.
Associate, Electrical Engineering; Wood Harbinger
Control Systems Engineer; Robert Bosch Corp.
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.