# How the power distribution grid works

## Electrical power travels from the power plant to the industrial plant through the power distribution grid. All commercial electrical generators of any size generate three-phase ac.

03/01/2001

Electrical power travels from the power plant to the industrial plant through the power distribution grid. All commercial electrical generators of any size generate three-phase ac. The power transmission and distribution grids use ac because it has significantly less line loss than dc when transmitted over long distances. Also, transformers must have ac to operate. The power distribution grid depends on transformers.

The power plant produces three phases of power simultaneously. These phases are offset electrically by 120 deg. Four wires come from every power plant: three phases plus a neutral at ground potential, electrically, which is common to all three. An advantage of three-phase power is that at any given moment, one of the three is nearing a peak. Because of this situation, equipment such as high-power industrial three-phase motors and welding machines has smooth power output.

"Ground" in the power distribution grid is literally "the ground." The power company uses the earth as one of the wires in the power system. The earth is a good electrical conductor because it makes a good return path for electrons.

Three-phase power leaves the generator and enters a transmission substation at the power plant. This substation uses large transformers to convert the generator's voltage, which is at thousands of volts, to extremely high voltages for long-distance transmission on the transmission grid. Typical voltages for long-distance transmission are in the 155,000-765,000-V range to reduce line loss. A typical maximum transmission distance is about 300 miles.

Voltage is stepped-down from the transmission grid to the distribution grid. The conversion from "transmission" to "distribution" occurs in a power substation, which typically performs several functions.

• Transformers step transmission voltages (in the tens or hundreds of thousands of volts range) down to distribution voltages (typically less than 10,000 V).

• A bus splits the distribution power off in multiple directions.

• Circuit breakers and switches disconnect the substation from the transmission grid or the distribution lines from the substation when necessary.

• Power goes from the substation transformer to the distribution bus. This bus distributes power to separate sets of distribution lines, some possibly at different voltages. Transformers attached to the bus step the power down to standard line voltage (usually 7200 V) for one set of lines, while power leaves in other directions at different voltages if necessary. The higher-than-standard voltages are stepped down at other substations or in small transformers somewhere down the line.

Regulator banks prevent undervoltage and overvoltage conditions, and are located along the line either underground or in the air. Typically, there are switches that allow the regulator bank to be disconnected for maintenance when necessary.

At the plant

Plants typically have a substation that receives the incoming power, typically at 7200 V, and steps it down to the highest voltage used. Most plants use three-phase electrical power at 460-V ac. However, there are some plants that use 575-V ac and others 208-V ac.

Some plants require voltages much higher than 460-V ac, usually to run large motors. At the plant's substation, another feed is provided for a separate electrical service. The voltage for this extra connection is typically 6600-V ac. However, there are some plants that require 4160-V ac.

The stepped-down, three-phase 460-V ac electrical power enters the plant through switchgear, which provides for controlling, switching, metering, electrical protection, and power regulation. The power is then fed throughout the plant and distributed wherever electricity is needed.

The Top Plant program honors outstanding manufacturing facilities in North America. View the 2017 Top Plant.
The Product of the Year program recognizes products newly released in the manufacturing industries.
Each year, a panel of Control Engineering and Plant Engineering editors and industry expert judges select the System Integrator of the Year Award winners in three categories.
SCCR, 2018 Maintenance study, and VFDs in a washdown environment.
Welding ergonomics, 2017 Salary Survey, and surge protection
2017 Top Plant winner, Best practices, Plant Engineering at 70, Top 10 stories of 2017
Product of the Year winners, Pattern recognition, Engineering analytics, Revitalize older pump installations
Control room technology innovation; Practical approaches to corrosion protection; Pipeline regulator revises quality programs
The cloud, mobility, and remote operations; SCADA and contextual mobility; Custom UPS empowering a secure pipeline
Setting internal automation standards
Knowing how and when to use parallel generators

### Annual Salary Survey

Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.

There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.

But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.

Maintenance and reliability tips and best practices from the maintenance and reliability coaches at Allied Reliability Group.
The One Voice for Manufacturing blog reports on federal public policy issues impacting the manufacturing sector. One Voice is a joint effort by the National Tooling and Machining...
The Society for Maintenance and Reliability Professionals an organization devoted...
Join this ongoing discussion of machine guarding topics, including solutions assessments, regulatory compliance, gap analysis...
IMS Research, recently acquired by IHS Inc., is a leading independent supplier of market research and consultancy to the global electronics industry.
Maintenance is not optional in manufacturing. Itâ€™s a profit center, driving productivity and uptime while reducing overall repair costs.
The Lachance on CMMS blog is about current maintenance topics. Blogger Paul Lachance is president and chief technology officer for Smartware Group.
The maintenance journey has been a long, slow trek for most manufacturers and has gone from preventive maintenance to predictive maintenance.
This digital report explains how plant engineers and subject matter experts (SME) need support for time series data and its many challenges.
This digital report will explore several aspects of how IIoT will transform manufacturing in the coming years.
Maintenance Manager; California Oils Corp.
Associate, Electrical Engineering; Wood Harbinger
Control Systems Engineer; Robert Bosch Corp.
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.