First Fieldbus Foundation H1 Device Couplers get registered
Fieldbus Foundation has registered the first Foundation fieldbus H1 device couplers. The new device coupler registration process is said to provide automation end users with greater assurance of the interoperability of independently manufactured fieldbus physical layer components. MooreHawke, a division of Moore Industries, and Pepperl+Fuchs are the first Foundation fieldbus device coupler supp...
Fieldbus Foundation has registered the first Foundation fieldbus H1 device couplers. The new device coupler registration process is said to provide automation end users with greater assurance of the interoperability of independently manufactured fieldbus physical layer components.
MooreHawke, a division of Moore Industries, and Pepperl+Fuchs are the first Foundation fieldbus device coupler suppliers to pass the registration process.
The Fieldbus Foundation's Foundation Device Coupler Test Specification (FF-846-1.1) defines a suite of vendor self-tests for fieldbus device couplers with spur short-circuit protection. The tests cover device coupler requirements as specified in the FF-816 FS 1.5 Physical Layer Profile, as well as the IEC 61158-2: 2003 standard. The registration process includes additional tests beyond the scope of these standards, which determine if a device coupler is fit for its intended purpose of preventing spur short-circuits from disrupting a fieldbus network.
The device coupler registration program initially addresses two classes of devices: Foundation device couplers and Foundation wiring blocks. Device couplers are a critical component of an H1 fieldbus network enabling connection of multiple field devices to the segment. Characteristically, these units will have ports for trunk-in, trunk-out and one or more spurs, with the requirement of spur short-circuit protection. Registered device couplers must be network-powered (dc/dc conversion is not included). Wiring blocks are simple devices with a minimum of one trunk input and one spur output. Registered wiring blocks may contain surge protection circuits, integral terminators or indicating LEDs, but cannot provide spur short-circuit protection.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.