Finding momentary drops
Problem: Momentary drops (or extremely short power outages) in control circuits are often intermittent in nature and a beast to locate with a volt-ohm meter or other visual techniques.
Problem: Momentary drops (or extremely short power outages) in control circuits are often intermittent in nature and a beast to locate with a volt-ohm meter or other visual techniques. These drops can cause strange or hazardous equipment operation, or just be an annoyance. Is there another way to locate the momentary drop?
Solution: Use a small, simple device with two pigtails and alligator clips on the ends. The other end of the pigtails terminate to a small "ice cube" style relay (120 Vac or whatever control circuit voltage is needed), which is mounted inside a plastic enclosure. The enclosure has a normally open pushbutton and a pilot light for a visual indicator.
After connecting to a point in the control circuit (usually behind/after the component to be tested), a depression on the pushbutton energizes the relay. A holding contact maintains the relay in the energized state after release of the button. Minor or short power interruptions caused by a defective limit switch, vibrating gate switch, or defective stopbutton usually show up as the relay drops out. It is typically sensitive and fast enough to pick up even extremely short power drops.
Continue moving within the circuit prior to or after whatever series elements are to be tested to locate the suspect component. The more frequent the anomaly, the quicker the problem is pinpointed.
Contributor: Larry J. Duzeski, Senior Electrical Engineer, Mirro Co., Manitowoc, WI
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.