# FAQs on arc flash: Understand, assess the dangers

## Littelfuse has compiled a series of questions related to arc flash and hazard prevention.

10/29/2012

Littelfuse has compiled a series of questions related to arc flash and hazard prevention.

Q: How much energy is in a typical arc-flash incident?

A: A phase-to-phase fault within a 480 V system with 20,000 A of fault current provides 9,600,000 W of power. Imagine that there is no arc protection and the fault is allowed to last for 200 ms. The resulting energy would be 1,920 kJ. TNT releases approximately 2,175 j/g when detonated, so this arc flash would approximately correspond to the detonation of 883 g of TNT.

The formula is as follows:

• Energy = (voltage x current) x duration = (480 V x 20,000 amp) x 200 ms =1,920 kJ

The formula clearly shows that the destruction depends on power over time, which is in fact the formula for energy. The main task of an arc flash relay is to quickly detect the release of power and limit its lifespan. It goes without saying that nobody would like to have a half a stick of dynamite sitting inside their installation, just waiting to explode. Adding an arc flash relay allows for the fault to be extinguished as quickly as 35 ms.

Q: Do arc flash relays lower the required level of personal protective equipment (PPE)?

A: There are two ways to lower the incident energy of an arc flash event: reducing the fault current or reducing the clearing time. Reducing the available energy could in turn lower the required PPE. Reducing the current can be achieved by using current-limiting fuses and—for single-phase faults—resistance grounding.

Reducing the clearing time typically is not possible when using overcurrent protection due to system coordination requirements. Current-based protection must have sufficient delay to prevent unnecessary tripping on momentary overload or current spikes, thus losing valuable reaction time.

Arc flash relays resolve this issue by detecting overcurrent and light, which allows for the quickest reaction time. This detection time is much faster than standard protection and circuit breakers, which means using an arc flash relay in combination with a circuit breaker will lower the incident energy and arc flash hazards. This results in an increase in worker safety, less fault damage, and improved uptime.

Since the arc-flash hazard has decreased, the associated PPE may also be lowered. The exact amount will depend on user setpoints, so it must be modeled in the system to determine the new incident energy and PPE.

Q: When working on an energized transformer, we use instantaneous settings at the feeder breaker relay. Can the arc flash relay bring any benefit?

A: According to IEEE 1584, the arcing current can be as low as 38% of the available bolted fault current. If the instantaneous trip setting of the circuit breaker is greater than the arcing current, the breaker could take seconds or minutes to open, thus creating a potentially dangerous arc flash condition.

In contrast, an arc flash relay can react very quickly regardless of the fault current, and initiate the tripping signal to open the breaker and clear the fault within 30 ms, lowering the arc-flash incident energy to a minimum.

Q: When designing a safety protocol, should a low-fault-current long–clearing-time hazard and a high-fault-current short-clearing-time hazard with the same incident energy be treated differently?

A: If the incident energy is the same, no. However, if the incident energy is more or less, NFPA 70E requires the worker to use arc rated clothing equal to or greater than the possible maximum incident energy.

Q: Is there a recommendation as to how often you need to update the arc flash label?

A: NFPA 70E Article 130.5 requires the arc flash analysis to be updated when major modifications occur and reviewed every five years, whichever occurs first.

Q: We recently completed an arc flash hazard assessment and have a few dangerous level categories. How can I tell if the arc flash relay is going to reduce those levels, and will that change the amount of PPE required?

A: We recommend you contact the engineer or engineering firm that performed the assessment and request that it re-run the study at that equipment using the arc flash relay to lower the hazards.

The Top Plant program honors outstanding manufacturing facilities in North America. View the 2015 Top Plant.
The Product of the Year program recognizes products newly released in the manufacturing industries.
Each year, a panel of Control Engineering and Plant Engineering editors and industry expert judges select the System Integrator of the Year Award winners in three categories.
Doubling down on digital manufacturing; Data driving predictive maintenance; Electric motors and generators; Rewarding operational improvement
2017 Lubrication Guide; Software tools; Microgrids and energy strategies; Use robots effectively
Prescriptive maintenance; Hannover Messe 2017 recap; Reduce welding errors
The cloud, mobility, and remote operations; SCADA and contextual mobility; Custom UPS empowering a secure pipeline
Infrastructure for natural gas expansion; Artificial lift methods; Disruptive technology and fugitive gas emissions
Mobility as the means to offshore innovation; Preventing another Deepwater Horizon; ROVs as subsea robots; SCADA and the radio spectrum
Research team developing Tesla coil designs; Implementing wireless process sensing
Commissioning electrical systems; Designing emergency and standby generator systems; Paralleling switchgear generator systems
Natural gas engines; New applications for fuel cells; Large engines become more efficient; Extending boiler life

### Annual Salary Survey

Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.

There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.

But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.

Maintenance and reliability tips and best practices from the maintenance and reliability coaches at Allied Reliability Group.
The One Voice for Manufacturing blog reports on federal public policy issues impacting the manufacturing sector. One Voice is a joint effort by the National Tooling and Machining...
The Society for Maintenance and Reliability Professionals an organization devoted...
Join this ongoing discussion of machine guarding topics, including solutions assessments, regulatory compliance, gap analysis...
IMS Research, recently acquired by IHS Inc., is a leading independent supplier of market research and consultancy to the global electronics industry.
Maintenance is not optional in manufacturing. It’s a profit center, driving productivity and uptime while reducing overall repair costs.
The Lachance on CMMS blog is about current maintenance topics. Blogger Paul Lachance is president and chief technology officer for Smartware Group.
The maintenance journey has been a long, slow trek for most manufacturers and has gone from preventive maintenance to predictive maintenance.
Featured articles highlight technologies that enable the Industrial Internet of Things, IIoT-related products and strategies to get data more easily to the user.
This digital report will explore several aspects of how IIoT will transform manufacturing in the coming years.
Maintenance Manager; California Oils Corp.
Associate, Electrical Engineering; Wood Harbinger
Control Systems Engineer; Robert Bosch Corp.
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.