Environmental Services Laboratory Relocation
New construction: Environmental Services Laboratory Relocation; Erdman Anthony
Location: West Palm Pearch, Fla.
Firm name: Erdman Anthony
Project type, building type: New construction, research/lab/high-tech
Project duration: 2.5 years
Project completion date: Feb. 29, 2012
Project budget for mechanical, electrical, plumbing, fire protection engineering only: $4.2 Million
Challenge 1: The owner desired to equip the building with a generator sized to provide backup electrical power for the entire building, including HVAC and those systems necessary to sustain normal operations. The challenge in achieving this requirement was to balance the cost of providing a generator sized to withstand the inrush associated with the simultaneous restart of motor-driven equipment with that of a generator sized to handle just steady-state loading.
Challenge 2: Another challenge was to devise a lighting control system that could execute a complex scheme whereby traditional manual switching was required during normal operating hours and automatic control, using occupancy sensors, was desired during off hours.
Solution 1: After evaluating the cost of both options, the design team settled on a generator with a lower rating sized basically to handle only the steady state loads. The inrush issue was resolved by providing a control scheme, implemented via the BAS, which would stagger the restart of major equipment upon transfer to generator power. This solution not only reduced the upfront cost of the backup power system but also minimized the overall space required for the system.
Solution 2: To achieve this, local lighting controllers were used on each floor, which not only achieved the desired functionality but also provided the owner with the luxury of making future control changes via simple programming without the need for rewiring.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.