Effective partial-load condition strategies
Take advantage of a variety of common technologies and systems to help minimize the energy and cost expenditure of any facility’s daily operations.
Because buildings don’t always (or typically ever) run at their peak design demand, taking advantage of a variety of common technologies and systems can help minimize the energy and cost expenditure of any facility’s daily operations.
Series temperature sensors, pressure sensors, flow measuring stations, flow meters, control valves, modulating dampers, variable frequency drives (VFDs), and electronically commutated motors (ECM) for fans and pumps are just a few examples of strategies that can be employed to bridge the gap between the peak mechanical, electrical, plumbing (MEP), and fire protection design and actual systems usage.
While a detailed description of the intricacies of VFD design is outside the scope of this article, it has fundamental pertinence due to its influence on system flow reduction and system pressure modulation. The VFD adjusts motor speed, which reduces the motor’s power consumption in reaction to system flow, applicable to major pumps and main fans of a building’s HVAC systems. Rather than a full horsepower motor, an “inverse duty” motor with a VFD would be trimmed to operate at reduced horsepower.
Theoretically, the power savings can be calculated from the aforementioned affinity law for power. Figure 1 illustrates VFD motor speed at a reduced system flow and head pressure. This control application trims down multiple subsystems in the building. Today’s VFDs are applicable to most major pumps and fans and have become a common addition to any large-capacity building.
Suzan X. Sun-Yuan is a senior associate and lead mechanical engineer with Environmental Systems Design. She has experience with super-tall buildings, food labs, and central plant designs and upgrades. Mohsen Aghai is a senior associate and lead electrical engineer with Environmental Systems Design. He has experience with super-tall, mixed-used, commercial, and governmental buildings as well as hospitals and central plant designs and upgrades.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.