Decrease arc flash risk with new motor control center option
The Allen-Bradley Centerline 2500 motor control center (MCC) ArcShield option from Rockwell Automation helps reduce arc flash hazards and protects against internal electrical arcs.
Allen-Bradley Centerline 2500 motor control center (MCC) ArcShield option from Rockwell Automation helps reduce arc flash hazards and protects against internal electrical arcs.
Milwaukee, WI – The Allen-Bradley Centerline 2500 motor control center (MCC) ArcShield option helps reduce arc flash hazards and protects against internal electrical arcs. This version of the Centerline 2500 MCC from Rockwell Automation provides arc flash protection in a low-voltage MCC per IEC/TR 61641:2008 for arcing durations up to 300 milliseconds.
“By containing the arc fault, the Centerline 2500 MCC helps reduce the potential of worker exposure to hazardous conditions,” said Sarah Larson, product manager, Rockwell Automation. “Users also benefit from the MCC’s compliance with global standards through eased installation, operation and troubleshooting.”
ArcShield provides a pressure-relief system that exhausts gases through the top of the enclosure, away from personnel and enclosures, without front ventilation. MCC features automatic shutters that isolate the distribution bus when removing units and insulated power bus closing plates located on the ends of each MCC lineup. In of an internal fault, arc containment latches help contain the blast.
The product is engineered to global standards IEC 60439-1 and IEC 60529. The MCC with built-in DeviceNet network and Allen-Bradley IntelliCenter software offers real-time MCC diagnostics and monitoring over DeviceNet, ControlNet or Ethernet, giving users access to motor status information.
Features include variable speed drives, soft starters, and electronic overload relays. With intelligent motor controls, users user can capture performance information and communicate it through a built-in DeviceNet network.
To accommodate local requirements, Centerline 2500 MCC offers three- and four-pole bus bar power systems. Continuous bus bracing offers uniform support and high short-circuit withstand ratings in type-tested enclosures. Also featured is high unit density with up to 24 modules in each column. Individual units can be withdrawn to expedite replacement, minimizing maintenance and downtime. Four lever-operated unit positions (connected, test, disconnected, and withdrawn) allow withdrawal and insertion without tools. Each position can be locked to reduce risk of load feeding, while maintaining control power and networking communication abilities.
Rockwell Automation Inc .
– Control Engineering News Desk
Register here and scroll down to select your choice of eNewsletters free.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.