Dataforth DSCA DIN-rail mount isolated analog signal conditioners
More than 370 models of Dataforth DSCA isolated analog DIN rail mount signal conditioning modules are said to provide Dataforth Instrument Class performance, outstanding accuracy, 3-way isolation, and pluggable screw terminal disconnects to simplify wiring and maintenance.
Dataforth Corp.'s family of DSCA isolated analog DIN rail mount signal conditioning modules consists of more than 370 models that provide Dataforth Instrument Class performance, outstanding accuracy, 3-way isolation, and pluggable screw terminal disconnects to simplify wiring and maintenance.
Ground loops, overvoltage protection
Input modules in the DSCA signal conditioner family accept millivolt, volt, milliamp, RTD, thermocouple, potentiometer, strain gage, dc LVDT, frequency, ac to true RMS, and 2-wire transmitter inputs.
Voltage input conditioners accept signals fromugh 10k ohms. The dc LVDT module provides excitation and accepts input ranges from ±1V to ±10V. Frequency input signals can be TTL or zero crossing. The two-wire transmitter module provides loop power and accepts a 4 to 20mA input signal. Isolated field-side current and voltage outputs also are available.
All DSCA modules have excellent stability over time, Dataforth says, and do not require recalibration. However, multi-turn potentiometers are accessible and provide non-interactive zero and span settings adjustable up toe measures 2.95-in. x 0.89-in. x 4.13-in. (75 mm x 22.5 mm x 105 mm). All modules mount to the standard DIN EN 50022 35mm rail.
Specifications: Dataforth DSCA family of modules
Designed for data acquisition, test and measurement, and control system applications, Dataforth DSCA modules are said to provide:
• 1,500 Vrms transformer isolation and 240 Vrms field-side protection;
• ANSI/IEEE C37.90.1 transient protection;
• True 3-way isolation;
• Wide supply voltage, 15 V to 30 V dc;
• Industry standard output of 0 to 10 V
• 4- to 6-pole low-pass filtering;
• Low output noise;
• -40 °C to +80 °C operating temperature and relative humidity can be up to 95% non-condensing;
• Screw terminals and plug-in terminal blocks to simplify wiring and maintenance;
• C-UL-US listed (Class I, Division 2, Groups A, B, C, D);
• CE and ATEX compliant; and
• Manufactured according to regulations of RoHS Directive 2003/11/EC.
- Edited by Mark T. Hoske, editor in chief, Control Engineering , www.controleng.com.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.