Damper leakage limits free cooling
Sidebar: Consulting-Speciyfing Engineer HVAC Technology Report
Most people familiar with HVAC equipment would be quick to recognize the benefits afforded by low-leakage dampers applied to mixed-air plenums in the context of the outdoor air damper. After all, a leaky outdoor air damper in a cold or hot and humid environment can lead to energy waste by imposing an unnecessary outdoor air conditioning load on the system, either when it is on minimum outdoor air or during unoccupied hours. Furthermore, the leakage in a cold environment can lead to frozen coils and subsequent water damage issues and repairs.
However, another factor comes into play when you consider the economizer dampers in a mild environment and look at what happens if the return damper does not seal well. Economizer-equipped systems in mild environments tend to spend a lot of time near or at the 100% outdoor air position. This is because the ambient temperatures are frequently in the range of the required discharge temperature.
For example, in San Francisco, there are 7,896 hours per year (out of a total of 8,760 hours) where the temperature is 50 to 75 F and the enthalpy is low enough to make it advantageous to cool a 100% outdoor airstream versus a recirculated airstream with minimum outdoor air. In a situation like this, outdoor air damper leakage, while a problem in theory, is not much of an issue from a practical standpoint. But a return damper leaking 10% to 15% when it is supposed to be fully closed, compromises the ability of the economizer to provide free cooling because it elevates the return temperature above the current outdoor air temperature.
For example, on a 55 F day, with 75 F return air and a 55 F discharge temperature requirement, a system leaking 10% of its return air when it is supposed to be on 100% outdoor air is delivering a 57 F mixed air temperature (not a 55 F mixed air temperature). As a result, many control systems would stage on mechanical cooling when it is not actually necessary if the damper quality was improved.
- Events & Awards
- Magazine Archives
- Oil & Gas Engineering
- Salary Survey
- Digital Reports
Annual Salary Survey
After almost a decade of uncertainty, the confidence of plant floor managers is soaring. Even with a number of challenges and while implementing new technologies, there is a renewed sense of optimism among plant managers about their business and their future.
The respondents to the 2014 Plant Engineering Salary Survey come from throughout the U.S. and serve a variety of industries, but they are uniform in their optimism about manufacturing. This year’s survey found 79% consider manufacturing a secure career. That’s up from 75% in 2013 and significantly higher than the 63% figure when Plant Engineering first started asking that question a decade ago.