Compact power hub released
Pepperl+Fuchs FieldConnex is a new compact power hub designed to deliver dense amounts of power in even demanding operating conditions.
Pepperl+Fuchs FieldConnex Compact Power Hub. Reportedly designed as a versatile, high performance power supply for larger process automation projects, the FieldConnex Compact Power Hub delivers eight segments of redundant power in less cabinet space than any other comparable power supply on the market. It supports intrinsically safe fieldbus segments according to Entity Ex ic or Ex nL classification, and the High-Power Trunk concept. These power modules are available for 21...23 V / 500 mA or 28...30 V / 500 mA operation.
With a footprint of 150 mm x 268 mm, the FieldConnex Compact Power Hub reportedly requires about one third less space than a comparable standard power module, with no compromise in performance and power. Delivering high performance and power in significantly less space is achieved through the use of especially selected high-performance components and an advanced passive impedance design resulting in minimum heat dissipation.
“The power supply modules that mount on the motherboard are just 12.5 mm. Depending on the module the typical power loss is only 1.3 or 1.6 watts, which promises a long service life with the most efficient control room cabinet-packing density available today. And because the FieldConnex Compact Power Hub is designed with built-in redundancy, two power modules are assigned to each segment. This means that exchanging a failed power module does not require any interruption of the power supply, and will not affect plan operation,” says Brian Traczyk, Product Manager, Pepperl+Fuchs.
The basic design concept of the FieldConnex Compact Power Hub is a compact motherboard that provides all necessary wiring connections and interfaces. All connections are plug-in with retaining screws for long lasting connections, even under continuous vibration. The motherboard is available in different versions to suit varied application needs, including customized interfaces for major DCS systems such as Yokogawa and Invensys. It can hold up to sixteen plug-in power modules to supply redundant power for up to eight FOUNDATION Fieldbus H1 segments. Modules are simply plugged in and safely secured without need for any tools.
The FieldConnex Compact Power Hub supports physical layer diagnostics. Users simply plug Pepperl+Fuchs optionally available Advanced Diagnostic Module (ADM) into the motherboard of the power module. The ADM serves as the link between the physical layer of the fieldbus infrastructure and the Advanced Diagnostic Manager running at the control room, and detects deteriorating signal quality long before it affects plant operation.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.