Carlo Gavazzi EM21 Series is a very compact 3-phase energy meter
Compact 3-phase energy meter from Carlo Gavazzi allows the user to configure the instrument for panel mounting (72 mm x 72 mm) or DIN-rail mounting, either as an energy meter or a transducer.
Carlo Gavazzi Inc., involved in design, manufacturing, and marketing of electronic equipment, has recently launched the EM21 Series, a very compact 3-phase energy meter is provided with an innovative detachable, connector-less and battery-less display. See more below image.
It allows the user to configure the instrument for panel mounting (72 x 72mm) or DIN-rail mounting, either as an energy meter or a transducer. Typically the transducer would only be DIN rail mounted, whereas the meter could be DIN rail mounted or panel mounted, therefore this is three energy devices in one housing, the company says. This general purpose three phase energy meter is suitable for active and reactive energy metering for cost allocation, but also for main electrical parameter measurement and retransmission (transducer function). Current measurements are carried out by means of external current transformers. Voltage measurements carried out either by means of direct connection (up to 400 V LL) or by means of potential transformers. The EM21 Series is provided with a pulse output for active energy retransmission. As an option, a two-wire RS-485 communication port is also available. The EM21 Series is compact and easy to install, thanks to its application-oriented programming procedure, downloadable setup software and the wrong phase-sequence warning.
Carlo Gavazzi EM21 Series energy monitoring device: key features
Some of the main technical features include:
• 72x72x65mm housing for both DIN-rail and panel mounting;
• Detachable LCD display;
• Instantaneous variables readout: 3 x 3 digits;
• Energy metering readout: 7 digits;
• Accuracy of
• Class B according to EN50470-3 (class 1 of EN62053-21), Class 2 (kvarh) according to EN62053-23;
• For 1-phase (2 wire), 2-phase (3 wire), 3-phase (3, 4 wire, balanced, unbalanced) systems for up to 400 V LL;
• CT connection (5A), TRMS measurement method;
• System variables: W, var, PF, Hz, kWh, kvarh (other variables available via RS-485);
• Single phase variables: A, VLL, VLN, PF (other variables available via RS-485);
• 1 pulse (opto-MOSFET) output (standard);
• RS485 port (optional);
• Self-powered supply voltage from 3-phase mains;
• IP50 protection degree (from the front); and
• cUL listed, CE approved.
Also read from Control Engineering :
- Carlo Gavazzi: compact 90 W power supplies ;
- Proximity Sensor Tutorial Video: Inductive and Capacitive Sensors ; and
- Carlo Gavazzi Wireless Photoelectric Sensor: Battery power avoids buried cables .
- Edited by Mark T. Hoske, editor in chief, Control Engineering , www.controleng.com.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.