BAS motor controls with auto run, predictive calibration
The BAS motor controls from Cerus Industrial accept dry voltage inputs and include other options like auto run and predictive calibration. One model accepts up to 600 V AC and motor loads up to 40 A.
The BAS motor controls from Cerus Industrial incorporate the company’s Smartstart Control Module for seamless integration with digital controls. The starters accept dry voltage inputs (wide range 12 V ac-250 V ac) for activation by control systems without interposing relays. Other control options include auto run, fireman’s override, fault, proof of flow (detects loss of load), and SmartStart predictive calibration (fault alarm). Integrated LED pilot lights and Hand/Off/Auto keypad are standard, simplifying unit setup and verification.
A single model accepts 208-600 V ac and motor loads up to 40 A, eliminating discrete thermal overloads and numerous contactor coil voltages typically required with other motor starters. The broad operating ranges enable distributors to eliminate thousands of dollars on unnecessary stock and mis-sizing issues.
Upon motor start-up, the electronic Smartstart overload allows the starter to look for a safe operating range based on motor starting current. If the starter isn’t calibrated within that range, an alarm is activated and the starter contactor is opened. This feature is meant to protect against operators increasing the overload to overcome motor jams or other impedances and to provide base line protection should the starter not be calibrated. The BAS with Smartstart also protects against locked rotor, stall, and other undesirable starting conditions.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.