ASHRAE publishes 2013 version of IAQ standard
The 2013 version of ASHRAE’s indoor air quality (IAQ) standard contains several revisions to help users better meet its requirements.
Newly published, ANSI/ASHRAE Standard 62.1-2013: Ventilation for Acceptable Indoor Air Quality, sets minimum ventilation rates and other requirements for commercial and institutional buildings.
The 2013 standard combines the 2010 standard and 10 published addenda to that edition, providing an easy-to-use consolidated standard. Specific information on the contents of each addendum and approval dates for each addendum are included in Informative Appendix J at the end of the standard.
The 2013 edition of the standard revises and improves the standard in several ways. A number of changes remove inconsistencies within the standard and improve clarity. Significant changes include:
- Table 6-2, Zone Air Distribution Effectiveness is modified to increase the ventilation effectiveness of underfloor air distribution systems that meet certain conditions.
- Requirements for the quality of water used in humidification systems are modified and clarified.
- Building level pressurization requirements were clarified, including adding a definition of “exfiltration.”
- A performance alternative to the prescriptive exhaust rates is added. This approach differs from the Indoor Air Quality Procedure, the existing performance-based method for setting supply ventilation rates, in that monitoring of the concentrations of contaminants of concern is required and provides the basis for control of exhaust flow rates.
- Some changes to the ventilation rates and space types in Table 6-1 are made. These add refrigerated warehouses and change the ventilation rate for sports related spaces to include a per occupant component which then allows the use of demand controlled ventilation in these spaces.
- The filtration requirement on air entering wetted cooling coils has been modified to change the MERV rating from 6 to 8. This change will reduce potential for particulate deposition on the coils that could lead to biological or other contamination on the coils.
- Toilet exhaust air that is cleaned to Class 1 may be recirculated.
- Events & Awards
- Magazine Archives
- Oil & Gas Engineering
- Salary Survey
- Digital Reports
Annual Salary Survey
Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.
There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.
But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.
Read more: 2015 Salary Survey