Arc-flash detection relay minimizes dangerous arc-fault energy
Schweitzer Engineering Laboratories Inc. (SEL) offers arc-flash detection (AFD) capability in the SEL-751A Feeder Protection Relay, providing automatic protection against dangerous arc-flash events. See photo.
Pullman, WA – Schweitzer Engineering Laboratories Inc. (SEL) offers arc-flash detection (AFD) capability in the SEL-751A Feeder Protection Relay, providing fully automatic protection against dangerous arc-flash events. Without AFD, the arc flash can cause severe personal injury, extensive equipment damage, and lengthy system outages. In contrast, AFD interrupts power to the arc flash before it can cause significant damage. Anyone with metal-clad switchgear will benefit from using the SEL-751A with AFD.
The SEL-751A AFD solution uses fiber-optic, arc-flash light sensors to detect the light produced by an arc-flash event. To prevent false tripping, the SEL-751A looks for an overcurrent that coincides with the light flash. When both conditions are met, the SEL-751A sends a trip signal to the circuit breaker in as fast as 2 ms. This fast tripping significantly reduces the damage-causing energy released by the arc-flash event.
“As a result of new NESC and NFPA requirements, many utilities and industrial companies are looking for ways to mitigate arc-flash hazards. The SEL-751A can reduce these hazards by stopping an arc-flash event before it escalates into a catastrophic, high-energy event,” said SEL R&D Manager Angelo D’Aversa.
For more information, see SEL-751A Feeder Protection Relay with AFD .
Also read from Control Engineering : Arc flash blowout.
- Edited by Mark T. Hoske , editor in chief
Control Engineering News Desk www.controleng.com
Register here to select your choice of free eNewsletters .
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.