Applying gain scheduling
Exploring a process scenario that may be a good place to apply a gain scheduling strategy.
Dear Control Engineering: I enjoyed your article about gain scheduling. I’m curious as to your thoughts about another variable gain scenario. Suppose a PID loop heats a measured but unregulated flowing stream. The changing flow rate would seem to change the response dynamics of the heating loop, requiring different tuning parameters. Is this a suitable case for implementing a gain schedule based on flowrate similar to your tank level application?
Thanks, Dale Cresap.
Vance VanDoren’s Back to Basics article drew a number of comments including this one. Here is Vance’s response:
Yes, I think it is. The time constant of your heating process probably lengthens as the flowrate goes up since a larger portion of the heat added by your PID loop is carried downstream, thereby increasing the time required to reach the setpoint. And since more heat is required to achieve the same temperature change, your process gain probably drops as the flowrate goes up. A gain schedule in your controller should help you combat those effects by forcing the controller to be more aggressive at higher flowrates.
I talked to Vance about his suggestion to clarify a couple points. First, we’re assuming that the temperature sensor feeds its signal to the PID controller, which modulates the heater. Vance thinks that setting the gain schedule based on flow can probably be done more easily from empirical data based on observation rather than a formula, although either could be possible.
I would add another thought, and ask which measuring device should be operative sensor. If the temperature is the wider variable and flow is less subject to change, then the discussion above is probably the way to go. On the other hand, if temperature is relatively stable and the flow can change more drastically, maybe it should be flowmeter? Of course that suggest a completely different control strategy, which we’ll leave for another time.
Peter Welander, pwelander(at)cfemedia.com
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.