Application case study: Upgrading flowmeter stabilizes control of process slurry flow
Poor performance from a flowmeter disrupts process stability, reduces output.
Replacing a faulty magmeter with new advanced design helped eliminate erratic flow signals, resulting in improved control of catalyst slurry flow.
Problem: An electromagnetic flowmeter measuring catalyst slurry containing 30% solids flowing through a 3-in. pipe continually produced erratic and erroneous flow readings, thwarting flow control efforts. The plant maintenance group tried various methods to correct its performance with no success. Meanwhile, operation under automatic control was impossible.
The graphic shows intermediate steps in the manufacture of catalyst, including the slurry flow control system. A centrifugal pump with variable-speed drive controls flow at a rate set by the DCS. Slurry goes to a belt filter that removes excess liquid and feeds moist catalyst cake into a gas-fired rotary dryer.
The magmeter sends flow measurements to a flow controller in a DCS control room. The operator sets the desired flow rate and the controller is supposed to keep the filtration and drying operations running smoothly and continuously at an optimum production rate. However, the original meter's flow signals were erratic and completely unpredictable. The signals could call for excessive rates of slurry flow that caused the dryer to flame out and shut down the line. The control room operator could not depend on the measured flow readings, which forced reliance on manual control.
Solution: Plant maintenance decided to substitute the new FSM4000 magnetic flowmeter from ABB Instrumentation. Upon installation, the new meter performed exceptionally well, producing reliable flow signals that allowed operation via automatic control.
ABB says the FSM4000’s success in dealing with noisy applications originates with its use of 70 Hz ac excitation of the primary's magnetic field, combined with advanced digital signal processing. The measurement signal has an accuracy of +/- 0.5 percent of rate, and offers fast response. With dependable flow control readings, the process is now on automatic control, improving production and eliminating troublesome shutdowns.
—Edited by Peter Welander, process industries editor, PWelander@cfemedia.com ,
Control Engineering Process Instrumentation & Sensors Monthly
Register here and scroll down to select your choice of free eNewsletters .
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.