24 V dc power with Ethernet specification
Like a round peg in a square hole, end-users can face incompatibility when designing and deploying 24 V auxiliary power on the factory floor. In response, ODVA is creating a "Power with Ethernet" specification for ODVA's networks based on Common Industrial Protocol (CIP). The 24 V dc auxiliary power specification is expected this month. Link to separate Power over Ethernet Plus information.
Like a round peg in a square hole, end-users can face incompatibility when designing and deploying 24 V auxiliary power on the factory floor. In response, ODVA is creating a "Power with Ethernet" specification for ODVA's networks based on Common Industrial Protocol (CIP). The 24 V dc auxiliary power specification is expected this month, according to reports made at the 2009 CIP Networks Conference & 13th Annual Meeting, Feb. 24–26.
The 24 V dc output power from an EtherNet/IP compatible device would run in a separate cable from the cable used for Ethernet data (as opposed to the IEEE Power over Ethernet, PoE, specification, which goes through the same wires), says Bob Lounsbury, chair for the ODVA EtherNet/IP Physical Layer Special Interest Group (SIG).
Total current in the system, as seen by power supply PS1, is the sum of the currents at each device (load): ltotal = IL1 + IL2 + IL3.
The power (actually 18–24 V dc depending on distance from the source) would operate e-stops, I/O sources and devices, actuators, and controllers—all of which may need more power than PoE or PoE-Plus wire can deliver, explains Lounsbury, who is also a principal engineer at Rockwell Automation. Work on the specification has involved several ODVA CIP groups, including the DeviceNet Physical Layer SIG. That group began considering 24 V dc power for CIP devices five years ago, covering topology, cable, and connectors. (The system is designed to provide no less than 18 V dc.)
Among details expected in the specification are support for:
Star, linear, and daisy chain topologies;
4-pin mini and micro connectors; and
5-pin IP67 connectors (compatible with Profibus).
Safety also is being considered, Lounsbury says, by ensuring male pins wouldn't be exposed, and trying to make sure damage wouldn't occur if cables were accidently plugged in where they shouldn't be.
Also read: Power over Ethernet Plus for factory automation . Have you looked at PoE and Power with Ethernet? Which is better for what? Share your views and experiences using the posting TalkBack tool below.
For other recent ODVA coverage, see:
Mark T. Hoske is Control Engineering editor in chief. Reach him at MHoske@cfemedia.com .
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.