Understanding speed when it comes to fieldbus networks
Fieldbus networks have a slow data transfer rate. Why can't they be faster?
Dear Control Engineering: I was reading the article about recent improvements to the Foundation fieldbus physical layer. It says that the data transfer rate is 31.25 kbit/sec. Isn’t that really slow? Why don’t they use a faster protocol?
You’re correct, 31.25 kbit/sec. is slow, and there are indeed much faster protocols. For starters, consider plain old USB that you see everywhere. USB 2 typically runs at 480 Mbit/sec., and USB 3 can hit 5 Gbit/sec. However, you have to look at it in context.
First, a device-level fieldbus does not have to carry large amounts of data. We’re talking about a process variable and a block of diagnostic information, so the file size is really small.
Second, the protocol is optimized to carry this kind of information. Ethernet is much faster, but it is very inefficient at carrying small packets of data because it has too much overhead. A fieldbus is typically better at this kind of application in spite of being slower.
Third, both Foundation fieldbus and Profibus PA (which use the same physical layer) are designed to run in hazardous environments. A slow data rate helps keep the power level very low. This is key for working in environments such as oil refineries.
Ultimately, it all comes down to the idea that a fieldbus protocol is purpose designed to perform very specific tasks in very specific conditions very efficiently. It does not have to serve as a mechanism to download photos from your phone one minute and communicate with an external disk drive the next. It may be slow, but it gets the job done.
Peter Welander, pwelander(at)cfemedia.com
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.