Transformer efficiency: Minimizing transformer losses
Distribution transformers and TP-1
Transformers that have primary voltages of 34.5 kV or less and secondary voltages of less than 600 V also must meet the efficiency ratings of TP-1 at a linear loading of 35%. However, TP-1 covers only 3-phase distribution transformers between 15 kVA and 1,000 kVA, so the larger transformers are not addressed by this standard. In addition, the distribution transformers are traditionally designed to be loaded to between 50% and 75%. As noted previously on the smaller, dry-type transformers, loadings that exceed the 35% TP-1 point will have significantly greater losses than the tabularized values. So while the goal of TP-1 was very lofty, it does not apply as well to actual installations.
Historically, it was common to see distribution transformers that had impedance ratings of 5.75%. As the electrical utilities have worked to reduce their operating costs, the impedance for distribution transformers has dropped to values as low as 1.5% impedance. Since the utilities typically absorb the transformer losses as a part of their operating costs, reducing the impedance percentage from 5.75% to 1.5% has saved more than 70% of their losses at the transformer. This turned out to be very convenient because TP-1 was requiring that these transformers have higher efficiencies at the same time that the utilities were attempting to reduce their operating costs.
This process had a negative side effect that was not immediately evident but had a major impact on the electrical engineer’s design: the available fault duty on the secondary of the transformer. A 1,000 kVA transformer with 5.75% impedance will have an available fault duty of 21,000 A at 480 V, assuming an infinite bus on the primary side. Given the same criteria for a 1.5% impedance transformer would result in an available fault duty of 80,000 A. The same transformer operating with a 120/208 V secondary will have available fault duties of 48,000 A and 185,000 A, respectively. This operating efficiency improvement has a major impact on the electrical system design, particularly at the lower secondary voltage of 120/208 V (see “Sizing stepdown transformers”).
While TP-1 did not address transformers that were rated larger than 1,000 kVA, there have been similar reductions in their impedances to affect matching savings for these larger transformers. As one would anticipate, available fault currents for a 2,500 kVA transformer are dramatically, though proportionally, larger. At 480 V, the fault duties would increase from 52,000 A to more than 200,000 A for a 1.5% impedance transformer. Thank goodness transformers of this size do not commonly come with a 208-V secondary, because the fault current would approach 500,000 A.
In the engineer’s quest to reduce energy consumption, matching the transformer to its anticipated load is critical in achieving that goal. By applying a 150-C rise transformer to a lightly loaded linear circuit, the losses noted in TP-1 will be very close to the actual losses. However, heavier transformer loadings will suggest the engineer design around one of the lower temperature-rise transformers, such as the 115 C or 80 C transformers. When there are significant harmonically rich loads that are to be fed by a dry transformer, the lowest losses are likely to be achieved by using K-rated transformers that are sized for the anticipated harmonic currents.
Injudicious transformer selection can exceed the losses shown in TP-1 by 300% to 400%, resulting in a negative return on investment for the increased cost of the higher efficiency transformers.
Know the loss data, loading when specifying transformers
In researching this article, the author found it quite interesting that published loss data for all of the major manufacturers queried was virtually nonexistent. When asking about losses for operating points other than the 35% loading for TP-1, there appeared to be nothing available. Also, loss data for transformers operating at 80-C rise, 115-C rise, and K-rated transformers were also unavailable. Asking your local transformer sales representative for loss data at the operating point to which you are designing and for the type of transformer that you are designing around may save your client many dollars in energy savings. However, inserting the standard 150-C rise transformer into your design, while planning on operating the transformer at a point other than 35% loading and with a significant percentage of nonlinear loads, could cost your client significantly over the life of a transformer.
Sizing stepdown transformers
One cautionary note on stepdown transformers: When transforming from 480 V to 120/208 V, these low-loss, dry-type transformers can sneak up on your design. With the higher impedances of yore, an engineer usually did not have to worry about having higher interrupting duty branch circuit breakers when they were connected downstream from a dry transformer and the rest of the distribution system was a fully rated system. With the lower impedances, transformers as small as 112.5 kVA can have available fault duties that would require the use of breakers with an interrupting duty of more than 10,000 A. When using dry transformers such as a 300 kVA, 480/120/208 V, available fault duties can exceed 40,000 A, requiring your electrical design to use 65,000 AIC breakers. It is better to break the 120/208 V load into small divisions so that the maximum transformer size does not exceed 75 kVA with an impedance of at least 2% and the lower interrupting breakers (read: less expensive) may be used.
Lovorn is president of Lovorn Engineering Assocs. He is a member of the Consulting-Specifying Engineer editorial advisory board.
Annual Salary Survey
After almost a decade of uncertainty, the confidence of plant floor managers is soaring. Even with a number of challenges and while implementing new technologies, there is a renewed sense of optimism among plant managers about their business and their future.
The respondents to the 2014 Plant Engineering Salary Survey come from throughout the U.S. and serve a variety of industries, but they are uniform in their optimism about manufacturing. This year’s survey found 79% consider manufacturing a secure career. That’s up from 75% in 2013 and significantly higher than the 63% figure when Plant Engineering first started asking that question a decade ago.