Scaling can sap energy, maintenance time
If some method can be found to control scaling, there is the potential to save energy and prevent equipment failure and reduce maintenance
Boil a kettle of tap water in a hard water area and two undesirable observations are made: A fine but harmless scum appears on the surface of the water and a hard white encrustation develops on the heating element. The latter is calcium carbonate and is usually referred to as limescale. The limescale that deposits on the heating element will, if untreated, reduce the efficiency of the kettle, induce corrosion of the element, and ultimately lead to appliance failure. However, it is not just domestic appliances that are affected; boilers and steam generators also develop limescale deposits, which will cause similar problems if left untreated.
Limescale can form wherever water is heated. The reason for the problem is that source waters (potable or ground water) contain dissolved mineral salts, sometimes described as hardness, which have low solubility in the water. When heated, the water can no longer hold these salts in solution and deposition must then occur.
What can go wrong?
Deposits are an insulting layer on heat transfer surfaces. This leads to more power being consumed or to the need to install heavier duty equipment to compensate. It is estimated that 40% more energy is needed to heat water in a system fouled with ¼-in. of limescale.
Scale in water lines reduces the available cross-section area and the throughput. Eventually the line will become completely blocked. Equipment then needs to be shut down for cleaning, and this costs money.
Safety valves or emergency process sensors (e.g., that operate deluge systems) may not operate in an emergency. Overheated boilers can be dangerous.
Stagnant conditions can develop in void spaces beneath deposits, and this encourages corrosion of steels and other metallic surfaces. The results can be fluid leaks and equipment failure, which is potentially dangerous. Scale surfaces are also excellent growth sites for bacteria, which can crate conditions hazardous to health (e.g., production of legionella pneumophila).
In order to establish if you have a problem, try answering these questions:
- Do appliances such as water-fed equipment contain white scale?
- Are there signs of unexpected deposit formation around valves or at the pipe outlets?
- Are boilers/heat exchangers performing below design?
- Is corrosion a problem in the plant?
- Is the water throughput less than expected?
The more times that the answer is "yes," then the more likely it is that you have scale.
- Events & Awards
- Magazine Archives
- Oil & Gas Engineering
- Salary Survey
- Digital Reports
- Survey Prize Winners
Annual Salary Survey
Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.
There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.
But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.
Read more: 2015 Salary Survey