Let’s discuss the copper
Data center owners are opting for even larger servers, adding even more copper.
Last week, we discussed the differences in construction costs and copper requirements between the competing approaches of locating medium-voltage transformations outdoors, and connecting the secondary loads via large underground duct banks, versus moving the transformations indoors, in close proximity to the loads.
The differences between the two approaches are becoming more pronounced recently, as more and more data center owners are opting for 230 V servers, and are distributing large critical power at 415 Y/240 V. That necessitates a full-size (and sometimes, an OVERSIZED) neutral, which adds at least another third to the tonnage and the cost of the copper in secondary feeders. I have seen some very large data center designs on the boards recently that will have more than 4 million lbs of copper in underground duct banks or cable tray, just to get 600, 480, or 415 V utility power and generator power into the low-voltage main distribution switchgear lineups, before the power is even distributed to any loads.
Some large data center owners who are moving to modular containers in their centers also have moved to switchgear containers and skid-mounted unit substations outdoors, close-coupling the transformations to the secondary switchgear. That removes all the copper between the transformer and the switchgear, but then adds back even MORE copper on the distribution feeders from the switchgear into the loads.
I’ve seen “modular” projects recently where the secondary switchgear was located outdoors, close-coupled to substation transformers, eliminating the need for a 4000 A or so secondary duct banks into the building. But those 4000 A trunk feeders were then replaced by branch distribution feeders in duct banks or cable tray having a total aggregate ampacity of 10,000 A or more, to distribute to the loads.
I think that this pronounced trend of load growth cries out more loudly than ever before in history for a real and true “loadcenter” approach, with the transformations located right down in the center of the loads, where little 4000 A braided flex links like these, connecting a transformer to its secondary switchgear, can replace all those duct banks and hundred of tons of copper.
If you can accept that this makes sense, what are the options? Until fairly recently, almost all of the loadcenter substation transformers that went inside data centers since 1995 were either VPI dry-type or epoxy cast coil construction.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.