International PUE agreement reached
An international agreement on power usage effectiveness (PUE) for measuring data center efficiency has been reached.
As more attention is focused on data centers and the amount of energy it takes to power them, more companies are finding the commercial and public relations value in undertaking Green IT projects, according to an internet.com blog by T. Lau . The problem, as I've blogged about previously, is that there is very little standardization on how to measure Green IT effectiveness and preventing outlandish or unprovable claims when it comes to how green a data center actually is. The EPA's forthcoming Energy Star for Data Centers program will go a long way towards establishing this common standard, but the program is for U.S.-based data centers only.
Over the weekend, news emerged of an international agreement to establish data center energy efficiency . The agreement is between The Green Grid (U.S.-based industry group), the U.S. Environmental Protection Agency, the European Commission Joint Research Centre, the Japan Ministry of Economy, Trade and Industry, and the Green IT Promotion Council (Japan-based industry group). For now the agreement is limited to these three regions, but could expand to include others such as China and India in the future.
The agreement establishes the Power Usage Effectiveness (PUE) as the "preferred energy efficiency metric ." Specifically, the agreement states the following shall be "guiding principles" as interim steps, and that data centers are "recommended" to measure PUE according to the principles:
- PUE is a measurement of the total energy of the data center divided by the IT energy consumption.
- The industry should improve IT measurement capability to enable take the measurement directly at the IT load (servers). At a minimum, IT energy measurements should be measured at the output of the UPS.
- For a dedicated data center, total energy measurement should include all energy sources at the point of utility handoff. For data centers in larger buildings, total energy should include all cooling, lighting, and support infrastructure in addition to IT load.
For more information, read:
- The full blog post by T. Lau on internet.com
- Data Center Power Use Effectiveness (PUE): Understanding the Contributing Factors
- Redefining the role of electrical engineers
- Tools, reports, and events for improving energy efficiency in data centers
- Webcast event: Uptime All the Time, No Matter What
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.