HP's newest data center opens with a unique cooling set up
In northeast England, HP's Wynyard Center opened this week with a unique cooling set up and an innovative design.
According to DatacenterDynamics , the HP Wynyard data center opened this week in northeast England. Contrary to the reports, the data center site will not be cooled by the wind. What will be cooled is filtered outside air.
What separates it from other mega scale data center sis the sign, which will see large volumes of slow moving air sucked in using 6.88-ft variable speed axial fans that service each data halls-there are four data halls currently available; one is live, one is being commissioned, and remaining two will take load later this year.
The eight inlet fans per data hall move the air through bag filters to a 16.4-ft sub-floor pressurized plenum. The air is then forced upwards through cold aisle contained cubes before passing through servers, being drawn out through the ceiling, and then re-circulated.
Eight exhaust fans draw the air out and pass it back over the data halls where it is mixed with outside air or where it can be fully re-circulated. Chiller capacity is available to augment the cooling when necessary and the chillers are also operated 200 hours/year to provide humidification.
To view the data center's floor plan, system configurations, and other diagrams, visit the DatacenterDynamics website here .
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.