Handling the heat
Using heat load information with thermal characteristics of the electrical room envelope engineers to establish a cooling load allows mechanical engineers to accurately select the size of their cooling system
Mechanical engineers will use the heat load information—together with the thermal characteristics of the electrical room envelope—to establish a cooling load. This cooling load will be used to size the selected cooling system. The cooling system selection is based on the geographic location of the building and the maximum inside and outside air (OA) temperatures.
If the building is located in a moderately cool and dry climate, OA ventilation may suffice. However, if the location is in a hot and/or humid climate, mechanical cooling will be needed.
When using ventilation for cooling, the cool OA is drawn into the space by exhaust fans without any portion of the air recirculating into the space. The amount of airflow required is inversely proportional to the difference between the design indoor temperature and the design OA temperature. A commonly used value for this difference is 10 F. This translates to a cooling load capacity at sea level of 3.22 W/sq ft at 1 cfm/sq ft.
The term "cfm" is the imperial unit commonly used by mechanical engineers for volumetric air. Note: Volumetric airflow requirements are highly dependent on the elevation above sea level. Therefore, the amount of cfm of cooling air required for an electrical room in Denver will be much higher than for the same electrical room located in Seattle.
When the OA cannot cool the electrical room, mechanical cooling will be required. In that case, the amount of cfm will be based on the temperature difference between the space and the supply air from the mechanical cooling unit. A common value for this difference is 30 F. Hence, when cooling with mechanical equipment, the amount of CFM may be as low as one-third the amount of cfm if using OA alone.
Madrigal is the mechanical engineering platform leader in Chicago for M+W Group. He has more than 20 years of experience in designing mechanical systems. His area of expertise is in the design of HVAC systems for critical environments in R&D laboratories, cleanrooms, high-energy accelerators, and mission critical facilities.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.