EC: Electronic Marshalling
Network Integration - I/O systems - Emerson Process Management - Electronic Marshalling enables I/O field wiring to land wherever you want, regardless of signal type or control strategy - eliminating the need for cross-wiring in marshalling cabinets. This is a Control Engineering 2011 Engineers' Choice (EC) Honorable Mention.
DeltaV digital automation system's Electronic Marshalling decouples process design from the I/O infrastructure design, to easily incorporate late process changes into the control system. With Electronic Marshalling, each terminal block has a channel characterization module (CHARM), which includes an A/D converter and associated characterization for different types of analog and digital I/O. Field wiring of any signal type can be terminated anywhere and characterized by the various CHARMs. A digital communication bus runs along the terminal strip to send device signal information to the redundant CHARM I/O card where I/O conditioning is complete. Any input value can be read by any DeltaV controller regardless of where the wiring is landed. DeltaV Electronic Marshalling eliminates the need for cross-wiring of the marshalling panel to the I/O cards.
Installation of Electronic Marshalling is easy, because it is similar to existing methods for terminating field wiring. No special training or expertise is needed to terminate wiring on the terminal blocks. An integrated €œknife-edge € disconnect eliminates the worry over accidently induced faults during hot cutovers and maintenance.
Trouble shooting of installation errors can be done on a channel-by-channel basis, because problems are isolated to a single channel , providing increased robustness. Because each CHARM comes fully equipped with the ability to read HART v7 data, intelligent field devices can be continuously monitored and quickly diagnosed. Redundancy ensures reliability: Redundant CHARM I/O Card; Redundant communications between CHARMs and the CHARM I/O Card; Redundant power between CHARM I/O Card to each CHARM; Redundant network communications between CAHRM I/O cards and controllers. Every project has late changes that can have significant impact on cost and schedule. Making these late changes is now easier because new field wiring can be added to cabinets at any time with no impact on the control system architecture.
Emerson Process Management
For more, see www.controleng.com/awards.
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
2012 Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.