# Decoding "efficiency" for mechanical draft fans

05/17/2013

Efficiency ranges

The efficiency and power requirements of a draft fan depend on the type and style of the blades used in a particular application (See Figure 2). These two variables have an opposite relationship to each other. For example, a fan with a low horsepower demand will have a high calculated efficiency.

Classically, fan blade designs are categorized in three major groups with relative efficiencies and degrees of power:

• Straight radial blade (RB) – lowest efficiency (65% to 72%) and therefore highest horsepower demand
• Radial tip (RT) – low efficiency (72% to 78%) and therefore high horsepower demand

Forward curved (FC) -  lower efficiency (72% to 76%) and therefore higher horsepower demand

Backward inclined (BI)

• Single thickness backward inclined flat (BF) - high efficiency (79% to 81%) and therefore low horsepower demand
• Single thickness backward curved (BC) – higher efficiency (80% to 82%) and therefore lower horsepower demand
• Dual thickness airfoil (AF) – highest efficiency (83% to 88%) and therefore lowest horsepower demand

Efficiency variations

A mechanical draft fan’s efficiency is dependent on the system pressure used in each calculation. System pressure requirements can take many different forms, leading to an array of ratings. The primary variations are defined below:

• Static pressure rise: Static pressure differential between the fan outlet and inlet: SPR = SP2 – SP1 (SPR = Static pressure rise; SP1 = SP2 = Static pressure at fan inlet and outlet)
• Fan total pressure: Total pressure differential between the fan outlet and inlet: FTP = TP2 – TP1 (FTP = Fan total pressure; TP1 = TP1 = Total pressure at fan inlet and outlet)
• Fan static pressure: This represents the pressure difference between the fan total pressure and the velocity pressure at the fan outlet: FSP = FTP – VP2 (FSP = Fan static pressure; VP2 = Fan outlet velocity pressure)

There are corresponding efficiencies associated with each of these pressures:

• Static efficiency (ȠSPR) is calculated utilizing static pressure rise. The relative comparison with other efficiencies can be mathematically expressed in the following form: ȠSSPR < Ƞt
• Fan total efficiency (Ƞt) is calculated utilizing fan total pressure and bears the following relationship to static efficiency and fan static efficiency:  Ƞt > ȠSPR> ȠS
• Fan static efficiency (ȠS) is calculated utilizing fan static pressure: ȠS < ȠSPR < Ƞt

The Air Movement and Control Association (AMCA), an association of air system equipment manufacturers, provides rating guidelines to ensure a common platform for the engineers, manufacturers, and users. However, each project is unique and ultimate project execution goals are subject to the interpretation of the players involved.

Evase effects

When calculating efficiency, static pressure regain due to an evase at the fan outlet may also be accounted for.

Evase output = Static pressure + (VP1 – VP2) x Conversion efficiency

Conversion efficiency may range from 60% to 80%. This has a dramatic effect on calculated efficiency and power input for some mechanical fan applications. Evase effectively reduces a fan’s working pressure requirements and thus reduces input power to the fan shaft. In order to avoid any confusion and to support fair comparisons, project specifications need to be abundantly clear if evase is to be considered when evaluating fans for efficiency.

Conclusion

Understanding the concepts of power and efficiency and their appropriate use in evaluation of the mechanical draft fans will undoubtedly help plants and engineers to clearly define the requirements and in return they will receive better response from the manufacturers. Evaluation of mechanical draft fans based on “efficiency” may not offer the desired benefit to the clients.

As discussed in this article, an apparent higher efficiency does not necessarily mean a lower input power to the fan. The clients are the rate payers and they pay for the actual power used to drive the fans. So, for relative comparisons, “input power to the fan” should be evaluated rather than the calculated efficiency.

Nurul “Moni” Talukder, PE, is a chief engineer in the Air Handling Group at ProcessBarron in Pelham, Ala. ProcessBarron is a leader in the design, manufacturing, installation, and maintenance of air and material handling equipment for heavy industry. Moni can be reached at: mtalukder@processbarron.com.

<< First < Previous Page 1 Page 2 Next > Last >>

The Top Plant program honors outstanding manufacturing facilities in North America. View the 2015 Top Plant.
The Product of the Year program recognizes products newly released in the manufacturing industries.
Each year, a panel of Control Engineering and Plant Engineering editors and industry expert judges select the System Integrator of the Year Award winners in three categories.
Doubling down on digital manufacturing; Data driving predictive maintenance; Electric motors and generators; Rewarding operational improvement
2017 Lubrication Guide; Software tools; Microgrids and energy strategies; Use robots effectively
Prescriptive maintenance; Hannover Messe 2017 recap; Reduce welding errors
The cloud, mobility, and remote operations; SCADA and contextual mobility; Custom UPS empowering a secure pipeline
Infrastructure for natural gas expansion; Artificial lift methods; Disruptive technology and fugitive gas emissions
Mobility as the means to offshore innovation; Preventing another Deepwater Horizon; ROVs as subsea robots; SCADA and the radio spectrum
Research team developing Tesla coil designs; Implementing wireless process sensing
Commissioning electrical systems; Designing emergency and standby generator systems; Paralleling switchgear generator systems
Natural gas engines; New applications for fuel cells; Large engines become more efficient; Extending boiler life

### Annual Salary Survey

Before the calendar turned, 2016 already had the makings of a pivotal year for manufacturing, and for the world.

There were the big events for the year, including the United States as Partner Country at Hannover Messe in April and the 2016 International Manufacturing Technology Show in Chicago in September. There's also the matter of the U.S. presidential elections in November, which promise to shape policy in manufacturing for years to come.

But the year started with global economic turmoil, as a slowdown in Chinese manufacturing triggered a worldwide stock hiccup that sent values plummeting. The continued plunge in world oil prices has resulted in a slowdown in exploration and, by extension, the manufacture of exploration equipment.

Maintenance and reliability tips and best practices from the maintenance and reliability coaches at Allied Reliability Group.
The One Voice for Manufacturing blog reports on federal public policy issues impacting the manufacturing sector. One Voice is a joint effort by the National Tooling and Machining...
The Society for Maintenance and Reliability Professionals an organization devoted...
Join this ongoing discussion of machine guarding topics, including solutions assessments, regulatory compliance, gap analysis...
IMS Research, recently acquired by IHS Inc., is a leading independent supplier of market research and consultancy to the global electronics industry.
Maintenance is not optional in manufacturing. It’s a profit center, driving productivity and uptime while reducing overall repair costs.
The Lachance on CMMS blog is about current maintenance topics. Blogger Paul Lachance is president and chief technology officer for Smartware Group.
The maintenance journey has been a long, slow trek for most manufacturers and has gone from preventive maintenance to predictive maintenance.
Featured articles highlight technologies that enable the Industrial Internet of Things, IIoT-related products and strategies to get data more easily to the user.
This digital report will explore several aspects of how IIoT will transform manufacturing in the coming years.
Maintenance Manager; California Oils Corp.
Associate, Electrical Engineering; Wood Harbinger
Control Systems Engineer; Robert Bosch Corp.
This course focuses on climate analysis, appropriateness of cooling system selection, and combining cooling systems.
This course will help identify and reveal electrical hazards and identify the solutions to implementing and maintaining a safe work environment.
This course explains how maintaining power and communication systems through emergency power-generation systems is critical.