Compact fusible switches for finger-safe circuit protection
AutomationDirect has added Gladiator compact fusible switches for circuit protection. They are also equipped with lockout/tagout capability and finger-safe construction.
Gladiator compact fusible switches have been added to AutomationDirect’s product offering of circuit protection devices. The single-pole, two-pole and triple-pole ac devices are available in Class CC and Midget fuse models; single-phase dc devices are also available. The 35 mm DIN rail mountable switches’ compact size reportedly takes up only one-third the space of a molded circuit breaker and two-thirds the space of traditional fusible switches, saving space in control panels. The full voltage rating of up to 600 V ac (80 V dc) apparently allows installation flexibility in many applications where feeder and branch circuit protection are required.
Equipped with lockout/tagout capability and finger safe construction, Gladiator switches promote safe workplace practices by preventing contact with live components. Open fuse indication provides faster troubleshooting and reduced downtime.
Class CC fuse models are UL98 listed and have a 200 kA Short-Circuit Current Rating; Midget Class fuse models are UL508 listed and have a 1 0kA Short-Circuit Current Rating. A 5A auxiliary contact with one normally-open and one normally-closed contact is also available.
- Edited by Chris Vavra, Control Engineering, www.controleng.com
Annual Salary Survey
After almost a decade of uncertainty, the confidence of plant floor managers is soaring. Even with a number of challenges and while implementing new technologies, there is a renewed sense of optimism among plant managers about their business and their future.
The respondents to the 2014 Plant Engineering Salary Survey come from throughout the U.S. and serve a variety of industries, but they are uniform in their optimism about manufacturing. This year’s survey found 79% consider manufacturing a secure career. That’s up from 75% in 2013 and significantly higher than the 63% figure when Plant Engineering first started asking that question a decade ago.