Choosing output formats for instrumentation transmitters
Why isn’t it easier to offer user selectability of signal format for field devices?
Dear Control Engineering: The article about new gas flowmeters says that the company is using a more modular transmitter that makes it easier for the user to select a signal format. Why aren’t more companies doing that? Having to change field devices is a major drag on trying to use a more sophisticated networking technology.
One of the more interesting aspects of the flowmeters that FCI has introduced is the modularity of its transmitter. While most devices are hard wired to one specific format (e.g., 4-20 mA with HART or Foundation fieldbus), these new devices offer a plug-in module to allow users to change the output format.
I don’t know if this is the first time somebody has done this, but it certainly is not a common feature. Typically a transmitter is indeed fixed to a given protocol. This fact has made the process of migrating to a more sophisticated networking protocol much more expensive. For example, if all the devices in a process unit use 4-20 mA or some older analog voltage signal, you’ll probably have to replace them all if you want to move to a fieldbus. FCI has promised that its new transmitter is future proof in the sense that if you do need to make such a change, you can change the module (assuming the right format is available) and not the whole device. The company plans on using this approach with larger portions of its product line as time goes on.
To my thinking, a typical flowmeter or pressure sensor ought to come with a universal transmitter that is software configurable or you set a group of DIP switches to give the connectivity you want. Set it yourself for anything from 4-20 mA, Modbus, USB, Profibus, Foundation fieldbus, or any number of industrial Ethernet flavors. Maybe we’ll even throw in wireless. That isn’t quite practical yet, but I doubt it is far away. Some protocols still depend on a dedicated ASIC which is probably why having a plug-in component is still a requirement. My approach is probably still much too expensive, but might be here sooner than you think.
Subscribe to our Process Instrumentation & Sensors eNewsletter.
Peter Welander, pwelander(at)cfemedia.com
Case Study Database
Get more exposure for your case study by uploading it to the Plant Engineering case study database, where end-users can identify relevant solutions and explore what the experts are doing to effectively implement a variety of technology and productivity related projects.
These case studies provide examples of how knowledgeable solution providers have used technology, processes and people to create effective and successful implementations in real-world situations. Case studies can be completed by filling out a simple online form where you can outline the project title, abstract, and full story in 1500 words or less; upload photos, videos and a logo.
Click here to visit the Case Study Database and upload your case study.
Annual Salary Survey
In a year when manufacturing continued to lead the economic rebound, it makes sense that plant manager bonuses rebounded. Plant Engineering’s annual Salary Survey shows both wages and bonuses rose in 2012 after a retreat the year before.
Average salary across all job titles for plant floor management rose 3.5% to $95,446, and bonus compensation jumped to $15,162, a 4.2% increase from the 2010 level and double the 2011 total, which showed a sharp drop in bonus.